# PALMER-BOWLUS FLOW EQUATIONS

## Transcription

PALMER-BOWLUS FLOW EQUATIONS
```PALMER-BOWLUS FLOW EQUATIONS
NOTE: Because of the throat configuration in the Palmer-Bowlus flumes, no single flow
equation will describe the head curve for all sizes of the flume. Following are two formulas for
each size unit that approximate the actual flow curve for the flume. “Q” represents CFS.
The short formula (a) in the first equation gives a close fit for most of the flumes operating
range, but will deviate slightly at the upper and lower ends of the curve.
The long formula (b) fits the flow curve over the entire flow range.
4" Palmer-Bowlus:
1.
Q = 1.73 x (H + .00588) 1.9573 or,
2.
Q =-0.000491374 + 0.052219H + 1.815283H2 - 3.352818H3 + 7.682511H4 + 79.0388H5 +
113.3232H6 - 2711.151H7 + 5131.661H8
6" Palmer-Bowlus:
1.
Q = 2.071 x (H + .005421) 1.9025 or,
2.
Q = -0.000252012 + 0.051932H + 2.872653H2 - 5.988129H3 + 5.207215H4 + 69.2287H5 89.3457H6 - 348.922H7 + 572.806H8
8” Palmer-Bowlus:
1.
Q = 2.537 x (H + .0 1456) 1.9724 or,
2.
Q = -0.002211174 + 0.144056H + 2.644594H2 - 2.468403H3 + 1.537941H4 + 18.920840H5
+4.9486H6 - 123.611H7 + 119.943H8
10” Palmer-Bowlus:
1.
Q = 2.843 x (H + .01610) 1.9530 or
2.
Q= -0.002568036 + 0.157007H + 3.717063H2 - 7.279155H3 + 12.957680H4 +10.044620H5
- 30.7575H6 - 3.989H7 + 20.724H8
12” Palmer-Bowlus:
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
1.
Q = 3.142 x (H + .017) 1.9362 or,
2.
Q= +0.001285249 + 0.160814H + 4.074878H2 - 4.868885H3 + 5.194802H4 + 5.391436H5 2.3493H6 - 15.932H7 + 11.682H 8
15” Palmer-Bowlus:
1.
Q = 3.574 x (H + .01682) 1.9062 or
2.
Q= -0.005446241 + 0.321892H + 3.703519H2 - 1.430430H3 + 2.165814H4 -10.406070H5 +
32.1713H6 - 36.007H7 + 13.225H8
18” Palmer-Bowlus:
1.
Q = 3.988 x (H + .01875) 1.8977 or,
2.
Q = +0.010862620 + 0.005188H + 6.702144H2 - 7.621502H3 + 5.159058H4 + 3.082969H5
-1.4116H6 - 3.676H7 +1.957H8
21” Palmer-Bowlus:
1.
Q = 4.223 x (H + .039) 1.9619 or,
2.
Q= -0.027504770 + 0.689056H + 4.144363H2 - 1.761823H3 + 1.672703H4 -0.342789H5 +
1.6492H6 - 2.110H7 + 0.656H8
24” Palmer-Bowlus:
1.
Q = 4.574 x (H + .0408) 1.9497 or,
2.
Q = - 0.002225281 + 0.420895H + 5.930978H2 - 3.470244H3 + 0.746696H4 + 3.182714H5
-2.1110H6 + 0.058H7 + 0.141H8
27” Palmer-Bowlus:
1.
Q = 4.97 x (H + .038) 1.9269 or,
2.
Q = - 0.009705140 + 0.354086H + 6.791781H2 - 3.986792H3 + 1.071059H4 + 2.255546H5 1.3530H6 - 0.005H7 + 0.084H8
30” Palmer-Bowlus:
1.
Q = 5.022 x (H + .0625) 1.9663 or,
2.
Q = -0.200116800 + 2.238534H + 2.207354H2 + 1.185735H3 + 0.374370H4 -0.386049H5 +
0.2800H6 - 0.168H7 + 0.033H8
36” Palmer-Bowlus:
1.
Q = 5.462 x (H + .08) 1.991 or,
2.
Q = -0.084205270 + 1.359937H + 5.845147H2 - 1.647873H3 + 0.509795H4 + 0.413952H5
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
-0.0570H6 - 0.105H7 + 0.0261H8
42” Palmer-Bowlus:
1.
Q = 6.12 x (H + .078) 1.9628 or,
2.
Q = - 0.083333500 + 1.431028H + 7.047561H2 - 2.475667H3 + 1.037684H4 +0.102303H5 0.0446H6 - 0.035H7 + 0.008H8
48” Palmer-Bowlus:
1.
Q = 6.626 x (H + .085) 1.9586 or,
2.
Q = - 0.053395340 + 1.441452H + 7.813287H2 - 2.012471H3 + 0.265820H4 +0.384576H5 0.0875H6 - 0.020H7 + 0.005H8
54” Palmer-Bowlus:
1.
Q = 7.210 x (H + .08625) 1.9450
60” Palmer-Bowlus:
1.
Q = 7.183 x (H + .126) 1.9833 or,
2.
Q = -0.614242800 + 4.007510H + 6.591763H2 - 1.186873H3 + 0.318855H4 + 0.215911H5
-0.0987H6 + 0.012H7 - 0.000H8
66” Palmer-Bowlus:
1.
Q = 8.536 x (H + .07820) 1.9100
72” Palmer-Bowlus:
1.
Q = 7.839 x (H + .155) 1.9871 or,
2.
Q =- 0.358481400 + 3.418848H + 8.675141H2 - 1.269805H3 + 0.156454H4 +0.085580H5 0.0048H6 - 0.005H7 + 0.001H8
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 4in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
0.01
0.02
0.03
0.04
0.05
0.00279
0.00408
0.00432
0.00631
1.9367
2.8327
0.06
0.07
0.08
0.09
0.10
0.00557
0.00725
0.00914
0.01124
0.01356
0.00861
0.01122
0.01414
0.01739
0.02098
3.8654
5.0359
6.3476
7.8058
9.4177
0.11
0.12
0.13
0.14
0.15
0.01612
0.01892
0.02198
0.02531
0.02891
0.02494
0.02927
0.03400
0.03915
0.04473
11.192
13.137
15.261
17.573
20.078
0.16
0.17
0.18
0.19
0.20
0.03280
0.03697
0.04142
0.04612
0.05107
0.05075
0.05720
0.06408
0.07136
0.07901
22.779
25.675
28.761
32.029
35.463
0.21
0.05623
0.08700
39.047
0.22
0.06157
0.09527
42.760
0.23
0.06707
0.10378
46.578
0.24
0.07269
0.11247
50.482
0.25
0.07841
0.12132
54.453
*For points listed below please see footnote 1.
0.26
0.27
0.28
0.29
0.30
0.31
0.08422
0.09012
0.09615
0.10241
0.10903
0.11623
0.13030
0.13943
0.14877
0.15845
0.16869
0.17983
58.483
62.580
66.772
71.116
75.713
80.715
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 6in
Palmer Bowlus Flume
(feet)
0.01
0.02
0.03
0.04
0.05
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
*For points listed below please see footnote 1.
0.36
0.20107
0.31110
139.63
0.37
0.21153
0.32728
146.90
0.38
0.22210
0.34363
154.23
0.39
0.23277
0.36015
161.65
0.00392
0.00571
0.00606
0.00883
2.7191
3.9633
0.06
0.07
0.08
0.09
0.10
0.00777
0.01010
0.01269
0.01552
0.01860
0.01203
0.01563
0.01963
0.02401
0.02877
5.3987
7.0169
8.8114
10.778
12.915
0.40
0.41
0.42
0.43
0.44
0.24358
0.25456
0.26579
0.27738
0.28946
0.37687
0.39386
0.41124
0.42916
0.44785
169.15
176.78
184.58
192.62
201.01
0.11
0.12
0.13
0.14
0.15
0.02192
0.02549
0.02931
0.03339
0.03774
0.03391
0.03943
0.04535
0.05166
0.05839
15.221
17.699
20.352
23.186
26.207
0.45
0.46
0.47
0.30223
0.31593
0.33089
0.46761
0.48882
0.51197
209.88
219.40
229.79
0.16
0.17
0.18
0.19
0.20
0.04237
0.04729
0.05251
0.05805
0.06392
0.06555
0.07317
0.08125
0.08982
0.09890
29.422
32.839
36.468
40.316
44.390
0.21
0.22
0.23
0.24
0.25
0.07013
0.07668
0.08357
0.09082
0.09842
0.10850
0.11863
0.12931
0.14052
0.15229
48.699
53.247
58.037
63.072
68.350
0.26
0.27
0.28
0.29
0.30
0.10637
0.11465
0.12326
0.13217
0.14137
0.16458
0.17740
0.19071
0.20450
0.21873
73.869
79.621
85.597
91.786
98.17
0.31
0.32
0.33
0.34
0.35
0.15083
0.16052
0.17042
0.18049
0.19071
0.23336
0.24836
0.26367
0.27926
0.29508
104.74
111.47
118.34
125.34
132.44
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 8in
Palmer Bowlus Flume
(feet)
0.01
MGD
CFS
GPM
(feet)
0.37
0.38
0.39
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
MGD
CFS
GPM
0.24923
0.38561
173.07
0.26277
0.27666
0.29087
0.30538
0.32017
0.33523
0.35051
0.36601
0.38170
0.39755
0.41355
0.40657
0.42806
0.45004
0.47249
0.49538
0.51867
0.54232
0.56630
0.59057
0.61510
0.63985
182.48
192.12
201.99
212.07
222.34
232.80
243.41
254.17
265.07
276.07
287.18
0.02
0.03
0.04
0.05
0.06
0.07
0.08
0.09
0.10
0.11
0.12
0.00493
0.00731
0.00999
0.01296
0.01622
0.01977
0.02360
0.02771
0.03209
0.00763
0.01131
0.01545
0.02005
0.02510
0.03059
0.03651
0.04287
0.04966
3.4247
5.0763
6.9363
9.0004
11.265
13.728
16.386
19.240
22.288
0.13
0.14
0.15
0.16
0.17
0.03677
0.04172
0.04696
0.05250
0.05833
0.05688
0.06455
0.07266
0.08122
0.09025
25.532
28.972
32.612
36.456
40.506
0.18
0.19
0.20
0.21
0.22
0.06446
0.07091
0.07768
0.08478
0.09222
0.09974
0.10972
0.12019
0.13118
0.14269
44.767
49.245
53.947
58.876
64.042
0.53
0.54
0.55
0.56
0.57
0.49540
0.51218
0.52916
0.54639
0.56395
0.76650
0.79246
0.81873
0.84539
0.87256
344.03
355.68
367.47
379.44
391.63
0.23
0.24
0.25
0.26
0.27
0.28
0.29
0.30
0.31
0.32
0.10001
0.10815
0.11666
0.12555
0.13481
0.14447
0.15452
0.16497
0.17582
0.18708
0.15473
0.16733
0.18050
0.19425
0.20859
0.22353
0.23908
0.25525
0.27204
0.28945
69.449
75.104
81.014
87.184
93.620
100.33
107.31
114.56
122.10
129.91
0.58
0.59
0.60
0.61
0.62
0.63
0.58194
0.60048
0.61972
0.63986
0.66110
0.68372
0.90040
0.92908
0.95885
0.9900
1.0229
1.0579
404.13
417.00
430.36
444.34
459.10
474.80
0.33
0.34
0.35
0.36
0.19873
0.21078
0.22322
0.23604
0.30748
0.32612
0.34537
0.36520
138.01
146.37
155.01
163.91
0.49
0.42968
0.66481
298.39
0.50
0.44593
0.68995
309.67
*For points listed below please see footnote
0.51
0.46230
0.71528
321.04
0.52
0.47878
0.74079
332.49
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 10in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.27970
0.29474
0.31025
0.32622
0.34265
0.43276
0.45603
0.48002
0.50474
0.53016
194.24
204.68
215.45
226.54
237.95
0.01
0.02
0.03
0.04
0.05
0.00596
0.00889
0.00923
0.01375
4.1417
6.1708
0.37
0.38
0.39
0.40
0.41
0.06
0.07
0.08
0.09
0.10
0.01217
0.01581
0.01978
0.02408
0.02869
0.01884
0.02446
0.03061
0.03726
0.04439
8.4541
10.980
13.739
16.722
19.923
0.42
0.43
0.44
0.45
0.46
0.35954
0.37687
0.39463
0.41281
0.43140
0.55629
0.58310
0.61058
0.63871
0.66748
249.68
261.71
274.05
286.67
299.58
0.11
0.12
0.13
0.14
0.15
0.03361
0.03882
0.04433
0.05014
0.05624
0.05199
0.06006
0.06859
0.07758
0.08702
23.337
26.959
30.787
34.820
39.057
0.47
0.48
0.49
0.50
0.51
0.45038
0.46973
0.48943
0.50947
0.52981
0.69684
0.72678
0.75726
0.78826
0.81974
312.76
326.20
339.88
353.80
367.92
0.16
0.17
0.18
0.19
0.20
0.21
0.06264
0.06934
0.07635
0.08366
0.09130
0.09926
0.09692
0.10729
0.11813
0.12945
0.14126
0.15358
43.502
48.154
53.019
58.100
63.403
68.934
0.52
0.53
0.54
0.55
0.56
0.57
0.55045
0.57135
0.59249
0.61386
0.63543
0.65719
0.85167
0.88400
0.91672
0.94978
0.98316
1.0168
382.25
396.77
411.45
426.29
441.27
456.38
0.22
0.23
0.24
0.25
0.26
0.10757
0.11621
0.12522
0.13460
0.14435
0.16643
0.17981
0.19375
0.20825
0.22335
74.698
80.704
86.959
93.470
100.25
0.58
0.67911
1.0507
471.60
0.59
0.70118
1.0849
486.93
0.60
0.72340
1.1193
502.36
For points listed below please see footnote 1.
0.61
0.74576
1.1539
517.89
0.27
0.28
0.29
0.30
0.31
0.15450
0.16505
0.17602
0.18741
0.19923
0.23905
0.25537
0.27234
0.28996
0.30826
107.29
114.62
122.24
130.14
138.36
0.62
0.63
0.64
0.65
0.66
0.76825
0.79089
0.81369
0.83667
0.85986
1.1887
1.2237
1.2590
1.2945
1.3304
533.51
549.23
565.06
581.02
597.13
0.32
0.33
0.34
0.21150
0.22421
0.23739
0.32724
0.34691
0.36729
146.87
155.70
164.85
0.67
0.68
0.69
0.88331
0.90708
0.93122
1.3667
1.4035
1.4408
613.41
629.91
646.68
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 10in
Palmer Bowlus Flume
0.35
0.36
0.25103
0.26513
0.38839
0.41021
174.32
184.12
0.72
0.73
0.74
0.75
0.76
0.77
0.78
1.0069
1.0336
1.0613
1.0902
1.1205
1.1525
1.1863
1.5579
1.5992
1.6421
1.6868
1.7337
1.7831
1.8355
699.23
717.77
737.01
757.08
778.12
800.31
823.85
0.70
0.71
0.95583
0.98101
1.4789
1.5179
663.77
681.26
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 12in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.38163
0.39951
0.41788
0.43674
0.45609
0.59046
0.61813
0.64656
0.67573
0.70568
265.02
277.44
290.19
303.29
316.73
0.01
0.02
0.03
0.04
0.05
0.01058
0.01637
7.3465
0.41
0.42
0.43
0.44
0.45
0.06
0.07
0.08
0.09
0.10
0.01425
0.01836
0.02288
0.02780
0.03312
0.02205
0.02840
0.03540
0.04302
0.05125
9.898
12.748
15.887
19.307
23.001
0.46
0.47
0.48
0.49
0.50
0.47594
0.49628
0.51711
0.53844
0.56026
0.73638
0.76785
0.80009
0.83309
0.86685
330.51
344.64
359.11
373.92
389.07
0.11
0.12
0.13
0.14
0.15
0.03882
0.04490
0.05135
0.05816
0.06533
0.06007
0.06948
0.07945
0.08999
0.10108
26.961
31.183
35.661
40.390
45.367
0.51
0.52
0.53
0.54
0.55
0.58256
0.60534
0.62860
0.65232
0.67649
0.90135
0.93660
0.97258
1.0093
1.0467
404.56
420.38
436.53
453.00
469.79
0.16
0.17
0.18
0.19
0.20
0.07285
0.08072
0.08893
0.09750
0.10641
0.11271
0.12489
0.13760
0.15085
0.16463
50.588
56.053
61.759
67.706
73.893
0.56
0.57
0.58
0.59
0.60
0.70111
0.72616
0.75162
0.77749
0.80375
1.0848
1.1235
1.1629
1.2030
1.2436
486.88
504.28
521.96
539.93
558.16
0.21
0.22
0.23
0.24
0.25
0.11566
0.12527
0.13523
0.14555
0.15622
0.17896
0.19382
0.20923
0.22519
0.24171
80.322
86.993
93.910
101.07
108.49
0.61
0.62
0.63
0.64
0.65
0.83037
0.85734
0.88465
0.91227
0.94018
1.2848
1.3265
1.3688
1.4115
1.4547
576.65
595.38
614.34
633.52
652.90
0.26
0.27
0.28
0.29
0.30
0.31
0.16726
0.17868
0.19047
0.20265
0.21521
0.22818
0.25880
0.27646
0.29470
0.31354
0.33299
0.35305
116.16
124.08
132.27
140.73
149.45
158.46
0.66
0.96837
1.4983
672.48
0.67
0.9968
1.5423
692.23
0.68
1.0255
1.5867
712.14
0.69
1.0544
1.6314
732.20
0.70
1.0835
1.6764
752.40
*For points listed below please see footnote 1.
0.32
0.33
0.34
0.35
0.24156
0.25535
0.26957
0.28422
0.37375
0.39509
0.41709
0.43975
167.75
177.33
187.20
197.37
0.71
0.72
0.73
0.74
1.1127
1.1422
1.1718
1.2015
1.7216
1.7672
1.8130
1.8590
772.73
793.17
813.72
834.38
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 12in
Palmer Bowlus Flume
0.36
0.29931
0.46310
207.85
0.75
1.2314
1.9052
855.13
0.37
0.38
0.39
0.40
0.31485
0.33084
0.34730
0.36422
0.48714
0.51189
0.53735
0.56354
218.64
229.75
241.18
252.93
0.76
0.77
0.78
0.79
1.2614
1.2916
1.3219
1.3523
1.9517
1.9983
2.0452
2.0924
875.97
896.92
917.97
939.13
0.80
1.3830
2.1398
960.42
0.81
0.82
0.83
0.84
0.85
1.4139
1.4450
1.4764
1.5081
1.5403
2.1876
2.2357
2.2843
2.3334
2.3832
981.85
1,003.5
1,025.3
1,047.3
1,069.7
0.86
0.87
0.88
0.89
0.90
1.5730
1.6062
1.6401
1.6749
1.7106
2.4337
2.4852
2.5377
2.5915
2.6467
1,092.3
1,115.4
1,139.0
1,163.1
1,187.9
0.91
0.92
0.93
0.94
1.7475
1.7856
1.8252
1.8666
2.7037
2.7627
2.8240
2.8880
1,213.5
1,240.0
1,267.5
1,296.2
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 15in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.06
0.07
0.08
0.09
0.10
0.01739
0.02248
0.02801
0.03398
0.04039
0.02691
0.03478
0.04334
0.05258
0.06249
12.079
15.611
19.451
23.598
28.047
0.46
0.47
0.48
0.49
0.50
0.54555
0.56767
0.59030
0.61345
0.63713
0.84409
0.87832
0.91333
0.94915
0.98578
378.85
394.22
409.93
426.01
442.45
0.11
0.12
0.13
0.14
0.15
0.04723
0.05449
0.06218
0.07029
0.07882
0.07307
0.08431
0.09621
0.10876
0.12195
32.796
37.843
43.183
48.815
54.737
0.51
0.52
0.53
0.54
0.55
0.66133
0.68608
0.71137
0.73721
0.76360
1.02323
1.06152
1.1006
1.1406
1.1815
459.26
476.44
494.00
511.95
530.28
0.16
0.17
0.18
0.19
0.20
0.21
0.22
0.23
0.24
0.25
0.26
0.27
0.28
0.29
0.30
0.08776
0.09711
0.10686
0.11702
0.12758
0.13854
0.14989
0.16165
0.17379
0.18633
0.19927
0.21260
0.22633
0.24046
0.25498
0.13578
0.15025
0.16534
0.18106
0.19740
0.21435
0.23192
0.25010
0.26890
0.28830
0.30832
0.32895
0.35019
0.37204
0.39452
60.944
67.436
74.210
81.265
88.598
96.208
104.094
112.254
120.69
129.40
138.38
147.64
157.17
166.98
177.07
0.56
0.57
0.58
0.59
0.60
0.61
0.62
0.63
0.64
0.65
0.66
0.67
0.68
0.69
0.70
0.79055
0.81806
0.84613
0.87477
0.90397
0.93373
0.96405
0.99493
1.02636
1.05833
1.0908
1.1239
1.1574
1.1915
1.2261
1.2232
1.2657
1.3092
1.3535
1.3986
1.4447
1.4916
1.5394
1.5880
1.6375
1.6878
1.7389
1.7908
1.8435
1.8970
548.99
568.10
587.59
607.48
627.75
648.42
669.48
690.92
712.75
734.95
757.53
780.47
803.78
827.44
851.44
0.31
0.32
0.33
0.34
0.35
0.26991
0.28525
0.30100
0.31716
0.33373
0.41762
0.44135
0.46571
0.49071
0.51636
187.44
198.09
209.02
220.25
231.76
0.71
0.72
0.73
0.74
0.75
1.2611
1.2966
1.3326
1.3690
1.4058
1.9512
2.0062
2.0618
2.1181
2.1750
875.77
900.43
925.40
950.67
976.23
0.36
0.37
0.38
0.39
0.40
0.35074
0.36817
0.38604
0.40435
0.42312
0.54267
0.56965
0.59730
0.62563
0.65466
243.57
255.68
268.08
280.80
293.83
0.76
0.77
0.78
0.79
0.80
1.4430
1.4805
1.5185
1.5567
1.5953
2.2326
2.2907
2.3494
2.4086
2.4683
1,002.06
1,028.15
1,054.49
1,081.1
1,107.8
0.41
0.42
0.43
0.44
0.44234
0.46202
0.48218
0.50281
0.68440
0.71485
0.74604
0.77796
307.18
320.85
334.84
349.17
0.81
0.82
0.83
0.84
1.6342
1.6733
1.7127
1.7523
2.5284
2.5890
2.6499
2.7112
1,134.8
1,162.0
1,189.4
1,216.9
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 15in
Palmer Bowlus Flume
0.45
0.52393
0.81064
363.84
0.85
1.7922
2.7729
1,244.6
0.86
1.8322
2.8349
1,272.4
0.87
1.8725
2.8972
1,300.3
0.88
1.9129
2.9597
1,328.4
0.89
1.9535
3.0226
1,356.6
0.90
1.9943
3.0857
1,385.0
*For points listed below please see footnote 1.
0.91
0.92
0.93
0.94
0.95
2.0353
2.0765
2.1179
2.1595
2.2014
3.1491
3.2128
3.2769
3.3413
3.4060
1,413.4
1,442.0
1,470.8
1,499.7
1,528.7
0.96
0.97
0.98
0.99
1.00
2.2436
2.2861
2.3290
2.3724
2.4164
3.4713
3.5371
3.6035
3.6707
3.7387
1,558.0
1,587.6
1,617.4
1,647.5
1,678.0
1.01
1.02
1.03
1.04
1.05
2.4610
2.5064
2.5527
2.6000
2.6486
3.8077
3.8780
3.9496
4.0228
4.0980
1,709.0
1,740.6
1,772.7
1,805.6
1,839.3
1.06
1.07
1.08
1.09
1.10
2.6985
2.7501
2.8035
2.8590
2.9169
4.1752
4.2550
4.3376
4.4235
4.5131
1,874.0
1,909.8
1,946.9
1,985.4
2,025.6
1.11
1.12
1.13
1.14
1.15
2.9775
3.0412
3.1083
3.1793
3.2547
4.6069
4.7054
4.8093
4.9192
5.0357
2,067.7
2,112.0
2,158.6
2,207.9
2,260.2
1.16
1.17
3.3349
3.4204
5.1598
5.2921
2,315.9
2,375.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 18in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.52813
0.55029
0.57291
0.59600
0.61956
0.81713
0.85143
0.88643
0.92215
0.95859
366.76
382.15
397.86
413.89
430.25
0.06
0.07
0.08
0.09
0.10
0.03263
0.03905
0.04610
0.05049
0.06042
0.07133
22.662
27.117
32.013
0.42
0.43
0.44
0.45
0.46
0.11
0.12
0.13
0.14
0.15
0.05377
0.06203
0.07086
0.08025
0.09019
0.08319
0.09597
0.10964
0.12417
0.13954
37.337
43.073
49.209
55.732
62.630
0.47
0.48
0.49
0.50
0.51
0.64359
0.66812
0.69314
0.71867
0.74472
0.9958
1.0337
1.0725
1.1120
1.1523
446.94
463.97
481.35
499.08
517.17
0.16
0.17
0.18
0.19
0.20
0.10065
0.11161
0.12308
0.13502
0.14744
0.15572
0.17269
0.19043
0.20891
0.22812
69.893
77.509
85.470
93.766
102.39
0.52
0.53
0.54
0.55
0.56
0.77129
0.79839
0.82603
0.85422
0.88297
1.1934
1.2353
1.2781
1.3217
1.3662
535.62
554.44
573.63
593.21
613.17
0.21
0.22
0.23
0.24
0.25
0.16032
0.17364
0.18741
0.20162
0.21625
0.24805
0.26867
0.28997
0.31195
0.33458
111.33
120.59
130.15
140.01
150.17
0.57
0.58
0.59
0.60
0.61
0.91228
0.94217
0.97264
1.0037
1.0353
1.4115
1.4577
1.5049
1.5529
1.6019
633.53
654.28
675.44
697.01
718.98
0.26
0.27
0.28
0.29
0.30
0.23130
0.24676
0.26264
0.27893
0.29563
0.35787
0.38180
0.40637
0.43157
0.45741
160.62
171.36
182.39
193.70
205.30
0.62
0.63
0.64
0.65
0.66
1.0676
1.1004
1.1339
1.1680
1.2027
1.6518
1.7026
1.7544
1.8071
1.8608
741.38
764.19
787.43
811.10
835.19
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.40
0.31273
0.33024
0.34816
0.36648
0.38521
0.40436
0.42392
0.44390
0.46430
0.48514
0.48387
0.51096
0.53868
0.56703
0.59601
0.62563
0.65590
0.68681
0.71838
0.75062
217.18
229.33
241.78
254.50
267.51
280.80
294.39
308.26
322.43
336.90
0.67
0.68
0.69
0.70
0.71
0.72
0.73
0.74
0.75
0.76
1.2380
1.2739
1.3105
1.3477
1.3855
1.4239
1.4630
1.5026
1.5429
1.5838
1.9155
1.9711
2.0276
2.0852
2.1437
2.2031
2.2636
2.3249
2.3873
2.4505
859.72
884.67
910.06
935.89
962.15
988.8
1,016.0
1,043.5
1,071.5
1,099.9
0.41
0.50641
0.78354
351.68
0.77
1.6253
2.5147
1,128.7
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 18in
Palmer Bowlus Flume
0.78
0.79
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
0.90
0.91
1.6674
1.7101
1.7533
1.7971
1.8415
1.8864
1.9319
1.9779
2.0243
2.0713
2.1188
2.1667
2.2150
2.2638
2.5798
2.6459
2.7128
2.7806
2.8492
2.9187
2.9891
3.0602
3.1321
3.2048
3.2782
3.3524
3.4272
3.5027
1,157.9
1,187.5
1,217.6
1,248.0
1,278.8
1,310.0
1,341.6
1,373.5
1,405.8
1,438.4
1,471.4
1,504.6
1,538.2
1,572.1
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
1.26
1.27
1.28
1.29
1.30
3.6370
3.6936
3.7507
3.8083
3.8665
3.9254
3.9850
4.0456
4.1070
4.1696
4.2334
4.2985
4.3652
4.4335
5.6273
5.7149
5.8032
5.8923
5.9823
6.0735
6.1658
6.2594
6.3545
6.4514
6.5501
6.6508
6.7540
6.8597
2,525.7
2,565.0
2,604.6
2,644.6
2,685.1
2,726.0
2,767.4
2,809.4
2,852.1
2,895.6
2,939.9
2,985.1
3,031.4
3,078.8
0.92
0.93
0.94
0.95
0.96
2.3130
2.3626
2.4126
2.4629
2.5135
3.5788
3.6555
3.7328
3.8106
3.8890
1,606.3
1,640.7
1,675.4
1,710.3
1,745.5
1.31
4.5037
6.9682
3,127.6
0.97
0.98
0.99
1.00
1.01
2.5645
2.6158
2.6674
2.7193
2.7714
3.9679
4.0473
4.1271
4.2073
4.2880
1,780.9
1,816.5
1,852.4
1,888.4
1,924.6
1.02
2.8238
4.3690
1,960.9
1.03
2.8764
4.4504
1,997.5
1.04
2.9292
4.5322
2,034.2
1.05
2.9823
4.6142
2,071.0
*For points listed below please see footnote 1.
1.06
3.0355
4.6967
2,108.0
1.07
1.08
1.09
1.10
1.11
3.0890
3.1427
3.1966
3.2507
3.3051
4.7794
4.8625
4.9459
5.0296
5.1137
2,145.1
2,182.4
2,219.9
2,257.5
2,295.2
1.12
1.13
1.14
1.15
1.16
3.3597
3.4145
3.4697
3.5251
3.5809
5.1982
5.2831
5.3684
5.4541
5.5404
2,333.1
2,371.2
2,409.5
2,448.0
2,486.7
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 21in
Palmer Bowlus Flume
(feet)
0.06
0.07
0.08
0.09
0.10
MGD
CFS
GPM
30.028
36.467
(feet)
0.46
0.47
0.48
0.49
0.50
MGD
0.69188
0.71827
0.74517
0.77258
0.80050
CFS
1.0705
1.1113
1.1529
1.1954
1.2386
GPM
480.47
498.80
517.48
536.51
555.90
0.04324
0.05251
0.06690
0.08125
0.11
0.12
0.13
0.14
0.15
0.06226
0.07249
0.08319
0.09436
0.10599
0.09634
0.11216
0.12871
0.14599
0.16399
43.238
50.340
57.770
65.526
73.605
0.51
0.52
0.53
0.54
0.55
0.82895
0.85792
0.88742
0.91746
0.9480
1.2826
1.3274
1.3730
1.4195
1.4668
575.66
595.78
616.27
637.13
658.37
0.16
0.17
0.18
0.19
0.20
0.21
0.22
0.23
0.24
0.25
0.26
0.27
0.28
0.29
0.30
0.11809
0.13064
0.14365
0.15712
0.17104
0.18541
0.20023
0.21549
0.23121
0.24737
0.26398
0.28103
0.29853
0.31648
0.33488
0.18271
0.20213
0.22226
0.24310
0.26463
0.28687
0.30979
0.33342
0.35773
0.38274
0.40843
0.43482
0.46190
0.48967
0.51814
82.004
90.72
99.76
109.11
118.78
128.75
139.05
149.65
160.56
171.78
183.32
195.16
207.31
219.78
232.56
0.56
0.57
0.58
0.59
0.60
0.61
0.62
0.63
0.64
0.65
0.66
0.67
0.68
0.69
0.70
0.9792
1.0109
1.0431
1.0759
1.1093
1.1433
1.1778
1.2129
1.2487
1.2850
1.3219
1.3594
1.3976
1.4364
1.4757
1.5150
1.5640
1.6139
1.6647
1.7164
1.7689
1.8223
1.8767
1.9320
1.9882
2.0453
2.1034
2.1624
2.2224
2.2833
679.99
701.99
724.38
747.17
770.35
793.94
817.93
842.32
867.13
892.35
917.99
944.06
970.5
997.5
1,024.8
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.40
0.41
0.42
0.43
0.44
0.45
0.35373
0.37302
0.39277
0.41298
0.43364
0.45475
0.47633
0.49838
0.52089
0.54387
0.56733
0.59127
0.61569
0.64059
0.66599
0.54729
0.57715
0.60771
0.63897
0.67093
0.70361
0.73700
0.77111
0.80594
0.84150
0.87779
0.91483
0.9526
0.9911
1.0304
245.64
259.04
272.76
286.79
301.14
315.80
330.79
346.10
361.73
377.69
393.98
410.60
427.56
444.85
462.49
0.71
0.72
0.73
0.74
0.75
0.76
0.77
0.78
0.79
0.80
0.81
0.82
0.83
0.84
0.85
1.5157
1.5564
1.5977
1.6396
1.6821
1.7253
1.7691
1.8136
1.8587
1.9045
1.9509
1.9980
2.0457
2.0940
2.1430
2.3452
2.4081
2.4719
2.5368
2.6026
2.6694
2.7372
2.8060
2.8759
2.9467
3.0185
3.0913
3.1651
3.2399
3.3157
1,052.6
1,080.8
1,109.5
1,138.6
1,168.1
1,198.1
1,228.6
1,259.4
1,290.8
1,322.6
1,354.8
1,387.5
1,420.6
1,454.2
1,488.2
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 21in
Palmer Bowlus Flume
0.86
2.1926
3.3925
1,522.7
*For points listed below please see footnote 1.
0.87
0.88
0.89
0.90
0.91
2.2429
2.2938
2.3454
2.3976
2.4504
3.4703
3.5491
3.6289
3.7096
3.7913
1,557.6
1,592.9
1,628.7
1,665.0
1,701.7
1.26
1.27
1.28
1.29
1.30
4.6199
4.6883
4.7569
4.8257
4.8947
7.1480
7.2538
7.3600
7.4664
7.5732
3,208.2
3,255.7
3,303.4
3,351.2
3,399.1
0.92
0.93
0.94
0.95
0.96
0.97
0.98
0.99
1.00
1.01
1.02
1.03
1.04
1.05
1.06
2.5038
2.5579
2.6125
2.6678
2.7236
2.7800
2.8370
2.8946
2.9527
3.0114
3.0706
3.1304
3.1907
3.2514
3.3127
3.8740
3.9576
4.0421
4.1276
4.2140
4.3013
4.3895
4.4786
4.5686
4.6594
4.7510
4.8434
4.9367
5.0307
5.1255
1,738.8
1,776.3
1,814.2
1,852.6
1,891.4
1,930.6
1,970.2
2,010.1
2,050.5
2,091.3
2,132.4
2,173.9
2,215.7
2,257.9
2,300.5
1.31
1.32
1.33
1.34
1.35
1.36
1.37
1.38
1.39
1.40
1.41
1.42
1.43
1.44
1.45
4.9638
5.0332
5.1027
5.1724
5.2423
5.3124
5.3827
5.4532
5.5239
5.5948
5.6660
5.7374
5.8092
5.8812
5.9537
7.6802
7.7875
7.8951
8.0029
8.1111
8.2195
8.3282
8.4373
8.5467
8.6564
8.7665
8.8771
8.9881
9.0996
9.2117
3,447.1
3,495.3
3,543.5
3,592.0
3,640.5
3,689.2
3,738.0
3,786.9
3,836.0
3,885.3
3,934.7
3,984.3
4,034.1
4,084.2
4,134.5
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
3.3744
3.4366
3.4993
3.5624
3.6259
3.6898
3.7542
3.8189
3.8839
3.9494
4.0151
4.0812
4.1476
4.2143
4.2813
5.2210
5.3173
5.4142
5.5118
5.6101
5.7090
5.8086
5.9087
6.0094
6.1106
6.2123
6.3146
6.4173
6.5205
6.6241
2,343.4
2,386.6
2,430.1
2,473.9
2,518.0
2,562.4
2,607.1
2,652.0
2,697.2
2,742.6
2,788.3
2,834.2
2,880.3
2,926.6
2,973.1
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
6.0265
6.0997
6.1735
6.2478
6.3226
6.3982
6.4744
6.5515
9.3243
9.4377
9.5518
9.6667
9.783
9.899
10.017
10.137
4,185.1
4,235.9
4,287.1
4,338.7
4,390.7
4,443.2
4,496.1
4,549.6
1.22
1.23
1.24
1.25
4.3485
4.4160
4.4837
4.5517
6.7281
6.8326
6.9374
7.0425
3,019.8
3,066.7
3,113.7
3,160.9
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 24in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.76790
0.79675
0.82610
0.85596
0.88631
1.1881
1.2328
1.2782
1.3244
1.3713
533.27
553.30
573.68
594.41
615.50
0.06
0.07
0.08
0.09
0.10
0.06192
0.09581
43.002
0.46
0.47
0.48
0.49
0.50
0.11
0.12
0.13
0.14
0.15
0.07198
0.08268
0.09399
0.10591
0.11843
0.11138
0.12792
0.14542
0.16387
0.18324
49.989
57.414
65.270
73.549
82.244
0.51
0.52
0.53
0.54
0.55
0.91718
0.9486
0.9805
1.0129
1.0458
1.4191
1.4676
1.5170
1.5672
1.6182
636.93
658.73
680.88
703.40
726.28
0.16
0.17
0.18
0.19
0.20
0.13154
0.14523
0.15949
0.17432
0.18970
0.20352
0.22471
0.24677
0.26971
0.29351
91.348
100.86
110.76
121.06
131.74
0.56
0.57
0.58
0.59
0.60
1.0793
1.1134
1.1479
1.1830
1.2187
1.6700
1.7226
1.7761
1.8304
1.8856
749.53
773.16
797.17
821.56
846.33
0.21
0.22
0.23
0.24
0.25
0.20563
0.22210
0.23910
0.25662
0.27467
0.31815
0.34363
0.36994
0.39705
0.42498
142.80
154.23
166.04
178.21
190.74
0.61
0.62
0.63
0.64
0.65
1.2550
1.2918
1.3291
1.3671
1.4056
1.9417
1.9987
2.0565
2.1152
2.1749
871.50
897.06
923.02
949.38
976.1
0.26
0.27
0.28
0.29
0.30
0.29323
0.31230
0.33188
0.35196
0.37254
0.45370
0.48321
0.51350
0.54456
0.57640
203.63
216.88
230.47
244.42
258.71
0.66
0.67
0.68
0.69
0.70
1.4448
1.4845
1.5249
1.5658
1.6074
2.2354
2.2969
2.3593
2.4227
2.4870
1,003.3
1,030.9
1,058.9
1,087.4
1,116.2
0.31
0.32
0.33
0.34
0.35
0.39361
0.41517
0.43722
0.45975
0.48277
0.60900
0.64236
0.67647
0.71134
0.74696
273.34
288.31
303.62
319.27
335.26
0.71
0.72
0.73
0.74
0.75
1.6496
1.6924
1.7359
1.7800
1.8247
2.5523
2.6185
2.6858
2.7540
2.8232
1,145.5
1,175.3
1,205.5
1,236.1
1,267.2
0.36
0.37
0.38
0.39
0.40
0.50627
0.53026
0.55473
0.57968
0.60511
0.78332
0.82043
0.85829
0.89689
0.9362
351.58
368.23
385.23
402.55
420.21
0.76
0.77
0.78
0.79
0.80
1.8701
1.9161
1.9629
2.0102
2.0583
2.8935
2.9647
3.0370
3.1103
3.1846
1,298.7
1,330.7
1,363.1
1,396.0
1,429.4
0.41
0.63102
0.9763
438.21
0.81
2.1070
3.2600
1,463.2
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 24in
Palmer Bowlus Flume
0.42
0.43
0.44
0.45
0.65742
0.68431
0.71168
0.73955
1.0172
1.0588
1.1011
1.1442
456.54
475.21
494.22
513.57
0.82
0.83
0.84
0.85
2.1564
2.2065
2.2573
2.3087
3.3365
3.4140
3.4925
3.5722
1,497.5
1,532.3
1,567.6
1,603.3
0.86
0.87
0.88
0.89
0.90
2.3609
2.4138
2.4673
2.5216
2.5765
3.6529
3.7346
3.8175
3.9014
3.9864
1,639.5
1,676.2
1,713.4
1,751.1
1,789.2
1.26
1.27
1.28
1.29
1.30
4.9958
5.0736
5.1517
5.2302
5.3092
7.7297
7.8499
7.9708
8.0924
8.2145
3,469.3
3,523.3
3,577.6
3,632.1
3,686.9
0.91
0.92
0.93
0.94
0.95
2.6322
2.6885
2.7456
2.8033
2.8618
4.0725
4.1597
4.2480
4.3374
4.4278
1,827.9
1,867.0
1,906.6
1,946.7
1,987.3
1.31
1.32
1.33
1.34
1.35
5.3885
5.4682
5.5483
5.6287
5.7094
8.3373
8.4606
8.5845
8.7089
8.8338
3,742.0
3,797.4
3,853.0
3,908.8
3,964.9
0.96
0.97
0.98
0.99
1.00
1.01
2.9209
2.9808
3.0413
3.1026
3.1645
3.2271
4.5194
4.6120
4.7057
4.8004
4.8962
4.9931
2,028.4
2,070.0
2,112.0
2,154.6
2,197.6
2,241.1
1.02
1.03
1.04
1.05
1.06
3.2905
3.3544
3.4191
3.4844
3.5504
5.0911
5.1901
5.2901
5.3912
5.4933
2,285.0
2,329.5
2,374.4
2,419.7
2,465.6
1.41
1.42
1.43
1.44
1.45
6.2001
6.2828
6.3657
6.4489
6.5323
9.5929
9.7209
9.849
9.978
10.107
4,305.6
4,363.0
4,420.6
4,478.4
4,536.3
1.07
1.08
1.09
1.10
1.11
3.6170
3.6843
3.7523
3.8208
3.8900
5.5964
5.7005
5.8056
5.9117
6.0188
2,511.8
2,558.6
2,605.7
2,653.4
2,701.4
1.46
1.47
1.48
1.49
1.50
6.6159
6.6998
6.7838
6.8681
6.9525
10.236
10.366
10.496
10.626
10.757
4,594.4
4,652.6
4,711.0
4,769.5
4,828.1
1.12
1.13
1.14
1.15
1.16
3.9598
4.0302
4.1013
4.1728
4.2450
6.1268
6.2357
6.3456
6.4563
6.5680
2,749.9
2,798.8
2,848.1
2,897.8
2,947.9
1.51
1.52
1.53
1.54
1.55
7.0372
7.1221
7.2072
7.2925
7.3780
10.888
11.019
11.151
11.283
11.415
4,886.9
4,945.9
5,005.0
5,064.2
5,123.6
1.17
1.18
1.19
4.3178
4.3910
4.4649
6.6806
6.7939
6.9082
2,998.4
3,049.3
3,100.6
1.56
1.57
1.58
7.4637
7.5497
7.6360
11.548
11.681
11.815
5,183.1
5,242.9
5,302.7
1.36
5.7905
8.9592
4,021.2
1.37
5.8718
9.0851
4,077.7
1.38
5.9535
9.2114
4,134.4
1.39
6.0354
9.3381
4,191.2
1.40
6.1176
9.4653
4,248.3
*For points listed below please see footnote 1.
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 24in
Palmer Bowlus Flume
1.20
1.21
4.5392
4.6141
7.0232
7.1391
3,152.2
3,204.2
1.59
1.60
7.7225
7.8093
11.948
12.083
5,362.8
5,423.1
1.22
1.23
1.24
1.25
4.6895
4.7654
4.8417
4.9186
7.2557
7.3731
7.4913
7.6101
3,256.6
3,309.3
3,362.3
3,415.7
1.61
1.62
1.63
1.64
7.8964
7.9838
8.0716
8.1598
12.218
12.353
12.489
12.625
5,483.6
5,544.3
5,605.3
5,666.5
1.65
8.2484
12.762
5,728.1
1.66
1.67
1.68
1.69
1.70
8.3375
8.4271
8.5172
8.6079
8.6992
12.900
13.039
13.178
13.318
13.460
5,789.9
5,852.1
5,914.7
5,977.7
6,041.1
1.71
1.72
1.73
1.74
1.75
1.76
8.7913
8.8841
8.9777
9.0722
9.1676
9.2642
13.602
13.746
13.891
14.037
14.184
14.334
6,105.1
6,169.5
6,234.5
6,300.1
6,366.4
6,433.4
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 27in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.11
0.12
0.13
0.14
0.15
0.08125
0.09267
0.10479
0.11762
0.13112
0.12572
0.14338
0.16214
0.18198
0.20288
56.427
64.354
72.774
81.678
91.057
0.51
0.52
0.53
0.54
0.55
1.0049
1.0389
1.0735
1.1086
1.1442
1.5548
1.6075
1.6610
1.7153
1.7704
697.84
721.48
745.49
769.86
794.60
0.16
0.17
0.18
0.19
0.20
0.14530
0.16014
0.17564
0.19177
0.20853
0.22481
0.24778
0.27175
0.29671
0.32265
100.90
111.21
121.97
133.17
144.81
0.56
0.57
0.58
0.59
0.60
1.1804
1.2171
1.2543
1.2921
1.3304
1.8263
1.8831
1.9407
1.9991
2.0584
819.70
845.18
871.04
897.27
923.88
0.21
0.22
0.23
0.24
0.25
0.22592
0.24392
0.26252
0.28171
0.30149
0.34955
0.37739
0.40617
0.43587
0.46648
156.89
169.39
182.30
195.63
209.37
0.61
0.62
0.63
0.64
0.65
1.3693
1.4087
1.4487
1.4892
1.5304
2.1185
2.1796
2.2414
2.3042
2.3678
950.9
978.3
1,006.0
1,034.2
1,062.8
0.26
0.27
0.28
0.29
0.30
0.32185
0.34278
0.36428
0.38633
0.40894
0.49798
0.53036
0.56362
0.59775
0.63272
223.51
238.04
252.97
268.29
283.99
0.66
0.67
0.68
0.69
0.70
1.5721
1.6144
1.6572
1.7007
1.7448
2.4324
2.4978
2.5641
2.6314
2.6996
1,091.7
1,121.1
1,150.9
1,181.1
1,211.7
0.31
0.32
0.33
0.34
0.35
0.43209
0.45579
0.48002
0.50478
0.53007
0.66855
0.70521
0.74270
0.78101
0.82014
300.06
316.52
333.35
350.54
368.11
0.71
0.72
0.73
0.74
0.75
1.7895
1.8348
1.8807
1.9272
1.9744
2.7687
2.8388
2.9099
2.9819
3.0548
1,242.7
1,274.1
1,306.0
1,338.4
1,371.1
0.36
0.37
0.38
0.39
0.40
0.55589
0.58223
0.60908
0.63646
0.66434
0.86009
0.90084
0.9424
0.9847
1.0279
386.03
404.32
422.97
441.98
461.35
0.76
0.77
0.78
0.79
0.80
2.0222
2.0707
2.1197
2.1695
2.2199
3.1288
3.2038
3.2797
3.3567
3.4347
1,404.3
1,438.0
1,472.0
1,506.6
1,541.6
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.69274
0.72166
0.75108
0.78101
0.81146
0.84241
0.87388
1.0718
1.1166
1.1621
1.2084
1.2555
1.3034
1.3521
481.07
501.15
521.58
542.37
563.51
585.01
606.86
0.81
0.82
0.83
0.84
0.85
0.86
0.87
2.2710
2.3227
2.3752
2.4283
2.4821
2.5366
2.5918
3.5137
3.5938
3.6749
3.7571
3.8404
3.9247
4.0101
1,577.1
1,613.0
1,649.4
1,686.3
1,723.7
1,761.5
1,799.8
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 27in
Palmer Bowlus Flume
0.48
0.49
0.50
0.90586
0.93836
0.9714
1.4016
1.4518
1.5029
629.07
651.64
674.56
0.88
0.89
0.90
2.6477
2.7043
2.7616
4.0966
4.1842
4.2728
1,838.7
1,878.0
1,917.8
0.91
0.92
0.93
0.94
0.95
2.8196
2.8784
2.9379
2.9981
3.0591
4.3626
4.4536
4.5456
4.6388
4.7331
1,958.1
1,998.9
2,040.2
2,082.0
2,124.3
1.31
1.32
1.33
1.34
1.35
5.7405
5.8277
5.9154
6.0036
6.0924
8.8819
9.0167
9.1524
9.2890
9.4264
3,986.5
4,047.0
4,107.9
4,169.2
4,230.9
0.96
0.97
0.98
0.99
1.00
1.01
1.02
1.03
1.04
1.05
3.1207
3.1832
3.2463
3.3102
3.3749
3.4403
3.5064
3.5733
3.6410
3.7093
4.8285
4.9251
5.0228
5.1217
5.2217
5.3229
5.4252
5.5287
5.6334
5.7392
2,167.2
2,210.5
2,254.4
2,298.8
2,343.7
2,389.1
2,435.0
2,481.5
2,528.4
2,575.9
1.36
1.37
1.38
1.39
1.40
1.41
1.42
1.43
1.44
1.45
6.1818
6.2717
6.3621
6.4531
6.5445
6.6365
6.7288
6.8217
6.9150
7.0087
9.5647
9.7038
9.844
9.984
10.126
10.268
10.411
10.555
10.699
10.844
4,292.9
4,355.4
4,418.2
4,481.3
4,544.8
4,608.6
4,672.8
4,737.3
4,802.1
4,867.2
1.06
1.07
1.08
1.09
1.10
3.7785
3.8484
3.9190
3.9904
4.0625
5.8462
5.9543
6.0636
6.1740
6.2856
2,623.9
2,672.5
2,721.5
2,771.1
2,821.2
1.46
1.47
1.48
1.49
1.50
7.1029
7.1974
7.2924
7.3877
7.4834
10.990
11.136
11.283
11.430
11.579
4,932.5
4,998.2
5,064.1
5,130.3
5,196.8
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
4.1353
4.2089
4.2833
4.3583
4.4341
4.5106
4.5878
4.6658
4.7444
4.8238
4.9038
6.3983
6.5122
6.6272
6.7433
6.8606
6.9790
7.0984
7.2190
7.3407
7.4635
7.5873
2,871.8
2,922.9
2,974.5
3,026.6
3,079.2
3,132.4
3,186.0
3,240.1
3,294.7
3,349.8
3,405.4
1.22
1.23
1.24
1.25
1.26
4.9845
5.0659
5.1480
5.2307
5.3141
7.7122
7.8381
7.9651
8.0931
8.2222
3,461.5
3,518.0
3,575.0
3,632.5
3,690.4
1.51
7.5794
11.727
5,263.5
1.52
7.6758
11.876
5,330.4
1.53
7.7725
12.026
5,397.6
1.54
7.8696
12.176
5,465.0
1.55
7.9669
12.327
5,532.6
1.56
8.0645
12.478
5,600.4
1.57
8.1624
12.629
5,668.4
1.58
8.2606
12.781
5,736.5
1.59
8.3591
12.933
5,804.9
1.60
8.4578
13.086
5,873.5
*For points listed below please see footnote 1.
1.61
1.62
1.63
1.64
1.65
8.5567
8.6559
8.7554
8.8550
8.9549
13.239
13.393
13.547
13.701
13.855
5,942.2
6,011.1
6,080.1
6,149.3
6,218.7
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 27in
Palmer Bowlus Flume
1.27
1.28
1.29
1.30
5.3982
5.4828
5.5681
5.6540
8.3522
8.4832
8.6152
8.7481
3,748.7
3,807.5
3,866.7
3,926.4
1.70
9.4575
14.633
6,567.7
1.71
1.72
1.73
1.74
1.75
9.5587
9.6601
9.762
9.864
9.966
14.790
14.946
15.104
15.261
15.419
6,638.0
6,708.4
6,779.0
6,849.8
6,920.7
1.76
1.77
1.78
1.79
1.80
10.068
10.171
10.274
10.377
10.481
15.578
15.737
15.896
16.056
16.216
6,991.8
7,063.1
7,134.6
7,206.3
7,278.2
1.81
1.82
1.83
1.84
1.85
1.86
1.87
1.88
1.89
1.90
1.91
1.92
1.93
1.94
1.95
1.96
1.97
10.585
10.689
10.794
10.899
11.004
11.111
11.217
11.324
11.432
11.541
11.650
11.760
11.871
11.983
12.096
12.210
12.325
16.377
16.538
16.700
16.863
17.026
17.191
17.356
17.521
17.688
17.856
18.025
18.196
18.367
18.541
18.715
18.891
19.069
7,350.4
7,422.9
7,495.6
7,568.6
7,641.9
7,715.6
7,789.7
7,864.2
7,939.1
8,014.5
8,090.4
8,166.8
8,243.9
8,321.6
8,399.9
8,479.0
8,558.9
1.66
1.67
1.68
1.69
9.0550
9.1553
9.2558
9.3566
14.010
14.165
14.321
14.477
6,288.2
6,357.8
6,427.7
6,497.6
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 30in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
1.0913
1.1273
1.1638
1.2009
1.2386
1.6885
1.7442
1.8007
1.8581
1.9164
757.87
782.85
808.21
833.97
860.13
0.11
0.12
0.13
0.14
0.15
0.08460
0.10336
0.12247
0.13090
0.15992
0.18949
58.750
71.78
85.05
0.51
0.52
0.53
0.54
0.55
0.16
0.17
0.18
0.19
0.20
0.14195
0.16178
0.18199
0.20257
0.22354
0.21962
0.25032
0.28158
0.31343
0.34586
98.57
112.35
126.38
140.68
155.23
0.56
0.57
0.58
0.59
0.60
1.2768
1.3156
1.3550
1.3950
1.4356
1.9755
2.0356
2.0965
2.1584
2.2212
886.68
913.6
941.0
968.8
996.9
0.21
0.22
0.23
0.24
0.25
0.24488
0.26662
0.28876
0.31130
0.33424
0.37889
0.41253
0.44678
0.48165
0.51715
170.06
185.16
200.53
216.18
232.11
0.61
0.62
0.63
0.64
0.65
1.4768
1.5185
1.5609
1.6039
1.6475
2.2849
2.3495
2.4151
2.4816
2.5491
1,025.5
1,054.5
1,084.0
1,113.8
1,144.1
0.26
0.27
0.28
0.29
0.30
0.35760
0.38137
0.40557
0.43020
0.45526
0.55329
0.59007
0.62751
0.66561
0.70438
248.33
264.84
281.65
298.75
316.15
0.66
0.67
0.68
0.69
0.70
1.6918
1.7367
1.7822
1.8283
1.8751
2.6176
2.6870
2.7574
2.8288
2.9012
1,174.8
1,206.0
1,237.6
1,269.6
1,302.1
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
0.49
0.48075
0.50670
0.53309
0.55994
0.58725
0.61503
0.64328
0.67200
0.70121
0.73091
0.76110
0.79179
0.82298
0.85469
0.8869
0.9196
0.9529
0.9867
1.0210
0.74384
0.78398
0.82482
0.8664
0.9086
0.9516
0.9953
1.0397
1.0849
1.1309
1.1776
1.2251
1.2733
1.3224
1.3722
1.4229
1.4744
1.5267
1.5798
333.86
351.87
370.20
388.85
407.81
427.10
446.72
466.67
486.95
507.58
528.54
549.85
571.52
593.53
615.90
638.64
661.74
685.21
709.05
0.71
0.72
0.73
0.74
0.75
0.76
0.77
0.78
0.79
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
1.9225
1.9706
2.0193
2.0687
2.1187
2.1695
2.2209
2.2729
2.3257
2.3791
2.4332
2.4880
2.5435
2.5997
2.6567
2.7143
2.7726
2.8316
2.8914
2.9745
3.0489
3.1243
3.2007
3.2782
3.3567
3.4362
3.5167
3.5983
3.6810
3.7647
3.8496
3.9354
4.0224
4.1104
4.1996
4.2898
4.3812
4.4736
1,335.1
1,368.4
1,402.3
1,436.6
1,471.3
1,506.6
1,542.3
1,578.4
1,615.0
1,652.2
1,689.7
1,727.8
1,766.3
1,805.4
1,844.9
1,884.9
1,925.4
1,966.4
2,007.9
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 30in
Palmer Bowlus Flume
0.50
1.0559
1.6337
733.27
0.90
2.9518
4.5672
2,049.9
0.91
0.92
0.93
0.94
0.95
3.0130
3.0749
3.1376
3.2009
3.2650
4.6618
4.7576
4.8545
4.9526
5.0517
2,092.4
2,135.4
2,178.9
2,222.9
2,267.4
1.31
1.32
1.33
1.34
1.35
6.0678
6.1593
6.2515
6.3443
6.4379
9.3883
9.5298
9.672
9.816
9.961
4,213.8
4,277.3
4,341.3
4,405.8
4,470.8
0.96
0.97
0.98
0.99
1.00
3.3299
3.3954
3.4617
3.5288
3.5966
5.1521
5.2535
5.3561
5.4598
5.5647
2,312.4
2,357.9
2,404.0
2,450.5
2,497.6
1.36
1.37
1.38
1.39
1.40
6.5322
6.6271
6.7227
6.8190
6.9160
10.107
10.254
10.402
10.551
10.701
4,536.2
4,602.2
4,668.6
4,735.4
4,802.8
1.01
1.02
1.03
1.04
1.05
3.6651
3.7344
3.8044
3.8751
3.9467
5.6707
5.7779
5.8862
5.9957
6.1064
2,545.2
2,593.3
2,641.9
2,691.1
2,740.7
1.41
1.42
1.43
1.44
1.45
7.0136
7.1119
7.2109
7.3105
7.4107
10.852
11.004
11.157
11.311
11.466
4,870.6
4,938.8
5,007.6
5,076.7
5,146.3
1.06
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
4.0189
4.0919
4.1657
4.2402
4.3155
4.3915
4.4682
4.5457
4.6240
4.7030
6.2182
6.3311
6.4453
6.5605
6.6770
6.7946
6.9134
7.0333
7.1544
7.2766
2,790.9
2,841.6
2,892.8
2,944.6
2,996.8
3,049.6
3,102.9
3,156.8
3,211.1
3,266.0
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
1.54
1.55
7.5116
7.6131
7.7152
7.8179
7.9213
8.0252
8.1297
8.2348
8.3405
8.4467
11.622
11.779
11.937
12.096
12.256
12.417
12.579
12.741
12.905
13.069
5,216.4
5,286.9
5,357.8
5,429.1
5,500.9
5,573.0
5,645.6
5,718.6
5,792.0
5,865.8
1.16
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
1.26
1.27
1.28
1.29
4.7828
4.8633
4.9445
5.0265
5.1093
5.1927
5.2770
5.3619
5.4476
5.5340
5.6212
5.7091
5.7977
5.8870
7.4000
7.5246
7.6503
7.7772
7.9052
8.0344
8.1647
8.2961
8.4287
8.5624
8.6973
8.8333
8.9704
9.1086
3,321.4
3,377.3
3,433.7
3,490.6
3,548.1
3,606.1
3,664.6
3,723.6
3,783.1
3,843.1
3,903.6
3,964.6
4,026.2
4,088.2
1.56
1.57
1.58
1.59
1.60
1.61
1.62
1.63
1.64
1.65
1.66
1.67
1.68
1.69
8.5535
8.6608
8.7687
8.8771
8.9860
9.0954
9.2053
9.3158
9.4267
9.5380
9.6499
9.762
9.875
9.988
13.234
13.400
13.567
13.735
13.903
14.073
14.243
14.414
14.585
14.758
14.931
15.104
15.279
15.454
5,939.9
6,014.4
6,089.4
6,164.6
6,240.3
6,316.3
6,392.6
6,469.3
6,546.3
6,623.6
6,701.3
6,779.3
6,857.6
6,936.2
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 30in
Palmer Bowlus Flume
1.30
5.9771
9.2479
4,150.7
1.71
10.216
15.806
7,094.2
1.72
10.330
15.983
7,173.7
1.73
10.445
16.161
7,253.4
1.74
10.560
16.339
7,333.4
1.75
10.676
16.518
7,413.6
*For points listed below please see footnote 1.
1.76
10.791
16.697
7,494.1
1.77
10.908
16.877
7,574.8
1.78
11.024
17.057
7,655.8
1.79
11.141
17.238
7,737.0
1.80
11.259
17.420
7,818.4
1.81
11.376
17.601
7,900.1
1.82
11.494
17.784
7,981.9
1.83
11.612
17.967
8,064.0
1.84
11.731
18.150
8,146.3
1.85
11.849
18.334
8,228.7
1.86
11.968
18.518
8,311.3
1.87
12.088
18.702
8,394.1
1.88
12.207
18.887
8,477.1
1.89
12.327
19.072
8,560.3
1.90
12.447
19.258
8,643.6
1.91
12.567
19.444
8,727.0
1.92
12.687
19.630
8,810.6
1.93
12.808
19.817
8,894.4
1.94
12.929
20.004
8,978.3
1.95
13.050
20.191
9,062.3
1.96
13.171
20.378
9,146.4
1.97
13.292
20.566
9,230.7
1.98
13.414
20.754
9,315.1
1.99
13.535
20.942
9,399.6
2.00
13.657
21.131
9,484.2
2.01
13.779
21.320
9,569.0
2.02
13.902
21.509
9,653.8
2.03
14.024
21.698
9,739
2.04
14.146
21.888
9,824
2.05
14.269
22.077
9,909
2.06
2.07
2.08
2.09
2.10
14.392
14.515
14.638
14.761
14.885
22.267
22.458
22.648
22.839
23.030
1.70
10.102
15.630
7,015.0
2.11
2.12
2.13
2.14
2.15
2.16
2.17
2.18
2.19
15.008
15.132
15.256
15.380
15.504
15.628
15.753
15.878
16.003
23.221
23.412
23.604
23.796
23.988
24.181
24.374
24.567
24.760
10,422
10,508
10,594
10,680
10,767
10,853
10,940
11,026
11,113
9,994
10,080
10,165
10,251
10,336
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 36in
Palmer Bowlus Flume
(feet)
MGD
CFS
0.11
0.12
0.13
0.14
0.15
0.15901
0.24603
0.16
0.17
0.18
0.19
0.20
0.17880
0.19926
0.22037
0.24214
0.26457
0.21
0.22
0.23
0.24
0.25
GPM
(feet)
MGD
CFS
GPM
110.43
0.51
0.52
0.53
0.54
0.55
1.2655
1.3073
1.3497
1.3927
1.4363
1.9580
2.0227
2.0883
2.1549
2.2223
878.83
907.86
937.3
967.2
997.4
0.27665
0.30830
0.34097
0.37465
0.40935
124.17
138.37
153.04
168.16
183.73
0.56
0.57
0.58
0.59
0.60
1.4805
1.5252
1.5706
1.6165
1.6631
2.2906
2.3599
2.4301
2.5011
2.5732
1,028.1
1,059.2
1,090.7
1,122.6
1,154.9
0.28764
0.31136
0.33571
0.36070
0.38632
0.44505
0.48174
0.51942
0.55809
0.59773
199.75
216.22
233.13
250.49
268.28
0.61
0.62
0.63
0.64
0.65
1.7102
1.7580
1.8063
1.8553
1.9048
2.6461
2.7200
2.7948
2.8705
2.9472
1,187.7
1,220.8
1,254.4
1,288.4
1,322.8
0.26
0.27
0.28
0.29
0.30
0.41257
0.43945
0.46694
0.49506
0.52379
0.63834
0.67992
0.72247
0.76597
0.81042
286.51
305.17
324.27
343.79
363.74
0.66
0.67
0.68
0.69
0.70
1.9550
2.0058
2.0572
2.1092
2.1618
3.0248
3.1034
3.1829
3.2634
3.3448
1,357.6
1,392.9
1,428.6
1,464.7
1,501.2
0.31
0.32
0.33
0.34
0.35
0.55313
0.58308
0.61364
0.64480
0.67657
0.85582
0.9022
0.9494
0.9977
1.0468
384.12
404.92
426.14
447.78
469.84
0.71
0.72
0.73
0.74
0.75
2.2150
2.2689
2.3234
2.3785
2.4343
3.4272
3.5105
3.5948
3.6801
3.7664
1,538.2
1,575.6
1,613.5
1,651.8
1,690.5
0.36
0.37
0.38
0.39
0.40
0.70894
0.74190
0.77546
0.80962
0.84437
1.0969
1.1479
1.1998
1.2527
1.3064
492.32
515.21
538.52
562.23
586.37
0.76
0.77
0.78
0.79
0.80
2.4907
2.5478
2.6055
2.6638
2.7228
3.8537
3.9420
4.0312
4.1215
4.2128
1,729.7
1,769.3
1,809.3
1,849.9
1,890.8
0.41
0.42
0.43
0.44
0.45
0.87971
0.9156
0.9522
0.9893
1.0270
1.3611
1.4167
1.4732
1.5306
1.5890
610.91
635.86
661.23
687.00
713.18
0.81
0.82
0.83
0.84
0.85
2.7824
2.8428
2.9037
2.9654
3.0277
4.3051
4.3984
4.4928
4.5881
4.6846
1,932.3
1,974.1
2,016.5
2,059.3
2,102.6
0.46
1.0653
1.6482
739.77
0.86
3.0907
4.7820
2,146.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 36in
Palmer Bowlus Flume
0.47
0.48
0.49
0.50
1.1041
1.1436
1.1837
1.2243
1.7084
1.7694
1.8314
1.8943
766.76
794.17
821.98
850.20
0.87
0.88
0.89
0.90
3.1544
3.2188
3.2838
3.3496
4.8806
4.9802
5.0808
5.1826
2,190.6
2,235.3
2,280.4
2,326.1
0.91
0.92
0.93
0.94
0.95
3.4160
3.4832
3.5511
3.6197
3.6890
5.2854
5.3893
5.4943
5.6004
5.7077
2,372.3
2,418.9
2,466.0
2,513.6
2,561.8
1.31
1.32
1.33
1.34
1.35
6.6979
6.7966
6.8961
6.9965
7.0978
10.363
10.516
10.670
10.825
10.982
4,651.3
4,719.8
4,789.0
4,858.7
4,929.0
0.96
0.97
0.98
0.99
1.00
3.7590
3.8297
3.9012
3.9734
4.0464
5.8160
5.9255
6.0361
6.1478
6.2607
2,610.4
2,659.5
2,709.2
2,759.3
2,810.0
1.36
1.37
1.38
1.39
1.40
7.1999
7.3028
7.4066
7.5113
7.6168
11.140
11.299
11.460
11.622
11.785
4,999.9
5,071.4
5,143.5
5,216.2
5,289.4
1.01
1.02
1.03
1.04
1.05
4.1201
4.1945
4.2697
4.3457
4.4224
6.3747
6.4899
6.6063
6.7238
6.8425
2,861.2
2,912.9
2,965.1
3,017.9
3,071.1
1.41
1.42
1.43
1.44
1.45
7.7231
7.8303
7.9384
8.0473
8.1570
11.949
12.115
12.282
12.451
12.621
5,363.3
5,437.7
5,512.8
5,588.4
5,664.6
1.06
1.07
1.08
1.09
1.10
4.4999
4.5782
4.6572
4.7371
4.8177
6.9624
7.0835
7.2058
7.3293
7.4540
3,125.0
3,179.3
3,234.2
3,289.6
3,345.6
1.46
1.47
1.48
1.49
1.50
8.2676
8.3790
8.4913
8.6044
8.7184
12.792
12.964
13.138
13.313
13.489
5,741.4
5,818.8
5,896.7
5,975.3
6,054.4
1.11
1.12
1.13
1.14
1.15
4.8991
4.9813
5.0642
5.1480
5.2326
7.5800
7.7071
7.8355
7.9652
8.0960
3,402.1
3,459.2
3,516.8
3,575.0
3,633.8
1.51
1.52
1.53
1.54
1.55
8.8332
8.9488
9.0652
9.1825
9.3006
13.667
13.846
14.026
14.207
14.390
6,134.1
6,214.4
6,295.3
6,376.7
6,458.7
1.16
1.17
1.18
1.19
1.20
5.3180
5.4042
5.4912
5.5791
5.6677
8.2282
8.3615
8.4962
8.6321
8.7693
3,693.1
3,752.9
3,813.3
3,874.3
3,935.9
1.56
1.57
1.58
1.59
1.60
9.4195
9.5392
9.660
9.781
9.903
14.574
14.759
14.946
15.133
15.322
6,541.3
6,624.4
6,708.1
6,792.4
6,877.2
1.21
1.22
1.23
1.24
5.7572
5.8475
5.9386
6.0306
8.9077
9.0474
9.1884
9.3307
3,998.1
4,060.8
4,124.1
4,187.9
1.61
1.62
1.63
1.64
10.026
10.150
10.274
10.399
15.513
15.704
15.897
16.090
6,962.5
7,048.4
7,134.8
7,221.8
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 36in
Palmer Bowlus Flume
1.25
6.1234
9.4743
4,252.4
1.65
10.525
16.285
7,309.3
1.26
1.27
1.28
1.29
1.30
6.2170
6.3115
6.4068
6.5030
6.6000
9.619
9.765
9.913
10.062
10.212
4,317.4
4,383.0
4,449.2
4,516.0
4,583.3
1.66
1.67
1.68
1.69
1.70
10.652
10.780
10.908
11.037
11.167
16.481
16.679
16.877
17.077
17.278
7,397.4
7,485.9
7,575.0
7,664.6
7,754.7
1.71
11.297
17.479
7,845.3
*For points listed below please see footnote 1.
1.72
1.73
1.74
1.75
1.76
11.428
11.560
11.693
11.826
11.960
17.682
17.887
18.092
18.298
18.505
7,936.4
8,028.0
8,120.1
8,212.7
8,305.7
2.11
2.12
2.13
2.14
2.15
17.003
17.155
17.307
17.459
17.612
26.307
26.542
26.778
27.014
27.250
11,808
11,913
12,019
12,125
12,231
1.77
1.78
1.79
1.80
1.81
12.095
12.230
12.366
12.503
12.640
18.714
18.923
19.133
19.345
19.557
8,399.2
8,493.2
8,587.6
8,682.5
8,777.9
2.16
2.17
2.18
2.19
2.20
17.765
17.919
18.072
18.226
18.380
27.487
27.724
27.962
28.200
28.439
12,337
12,443
12,550
12,657
12,764
1.82
1.83
1.84
1.85
1.86
12.778
12.917
13.056
13.195
13.336
19.770
19.985
20.200
20.416
20.633
8,873.6
8,969.8
9,066.4
9,163.4
9,260.9
2.21
2.22
2.23
2.24
2.25
18.535
18.689
18.844
19.000
19.155
28.678
28.917
29.157
29.397
29.637
12,871
12,979
13,086
13,194
13,302
1.87
1.88
1.89
1.90
1.91
13.477
13.618
13.760
13.903
14.046
20.851
21.070
21.290
21.510
21.732
9,358.7
9,456.9
9,555.5
9,654.5
9,754
2.26
2.27
2.28
2.29
2.30
19.311
19.467
19.623
19.780
19.936
29.878
30.120
30.361
30.604
30.846
13,410
13,519
13,627
13,736
13,845
1.92
1.93
1.94
1.95
1.96
14.189
14.333
14.478
14.623
14.769
21.954
22.177
22.401
22.625
22.850
9,854
9,954
10,054
10,155
10,256
2.31
2.32
2.33
2.34
2.35
20.093
20.251
20.408
20.566
20.724
31.089
31.333
31.576
31.821
32.065
13,954
14,063
14,172
14,282
14,392
1.97
1.98
1.99
2.00
2.01
14.915
15.061
15.208
15.356
15.503
23.076
23.303
23.531
23.759
23.987
10,357
10,459
10,561
10,664
10,766
2.36
2.37
2.38
2.39
2.40
20.883
21.042
21.201
21.360
21.520
32.311
32.556
32.802
33.049
33.296
14,502
14,612
14,723
14,833
14,944
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 36in
Palmer Bowlus Flume
2.02
2.03
2.04
2.05
2.06
15.652
15.800
15.949
16.099
16.249
24.217
24.447
24.677
24.908
25.140
10,869
10,972
11,076
11,180
11,284
2.41
2.42
2.43
2.44
2.45
21.680
21.841
22.002
22.163
22.325
33.544
33.793
34.042
34.291
34.542
15,056
15,167
15,279
15,391
15,503
2.07
2.08
2.09
2.10
16.399
16.549
16.700
16.851
25.373
25.606
25.839
26.073
11,388
11,493
11,597
11,702
2.46
2.47
2.48
2.49
22.487
22.650
22.813
22.977
34.793
35.045
35.297
35.551
15,616
15,729
15,843
15,956
2.50
23.142
35.806
16,071
2.51
2.52
2.53
2.54
2.55
23.307
23.473
23.639
23.806
23.974
36.061
36.317
36.575
36.834
37.093
16,185
16,300
16,416
16,532
16,649
2.56
2.57
2.58
2.59
2.60
24.143
24.313
24.483
24.655
24.827
37.355
37.617
37.881
38.146
38.413
16,766
16,884
17,002
17,121
17,241
2.61
2.62
2.63
25.001
25.176
25.352
38.682
38.952
39.225
17,362
17,483
17,605
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 42in
Palmer Bowlus Flume
(feet)
0.15
MGD
CFS
GPM
(feet)
0.55
MGD
CFS
GPM
1.6301
2.5221
1,132.0
1.6799
1.7303
1.7814
1.8331
1.8854
2.5992
2.6772
2.7562
2.8362
2.9172
1,166.6
1,201.6
1,237.1
1,273.0
1,309.3
0.16
0.17
0.18
0.19
0.20
0.25159
0.27622
0.30161
0.38926
0.42737
0.46666
174.71
191.82
209.45
0.56
0.57
0.58
0.59
0.60
0.21
0.22
0.23
0.24
0.25
0.32775
0.35464
0.38227
0.41063
0.43972
0.50711
0.54871
0.59146
0.63534
0.68035
227.61
246.28
265.47
285.16
305.36
0.61
0.62
0.63
0.64
0.65
1.9384
1.9920
2.0462
2.1011
2.1566
2.9991
3.0821
3.1660
3.2509
3.3368
1,346.1
1,383.3
1,421.0
1,459.1
1,497.7
0.26
0.27
0.28
0.29
0.30
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
0.49
0.50
0.46954
0.50007
0.53131
0.56327
0.59592
0.62927
0.66332
0.69806
0.73348
0.76958
0.80636
0.84381
0.88194
0.9207
0.9602
1.0003
1.0411
1.0825
1.1246
1.1673
1.2107
1.2547
1.2994
1.3447
1.3907
0.72648
0.77372
0.82207
0.87150
0.9220
0.9736
1.0263
1.0801
1.1349
1.1907
1.2476
1.3056
1.3646
1.4246
1.4856
1.5477
1.6108
1.6749
1.7400
1.8061
1.8732
1.9414
2.0105
2.0806
2.1517
326.07
347.27
368.97
391.16
413.83
437.00
460.64
484.76
509.36
534.43
559.97
585.98
612.46
639.39
666.79
694.65
722.97
751.74
780.96
810.64
840.77
871.35
902.37
933.8
965.8
0.66
0.67
0.68
0.69
0.70
0.71
0.72
0.73
0.74
0.75
0.76
0.77
0.78
0.79
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
0.90
2.2128
2.2696
2.3270
2.3851
2.4439
2.5032
2.5633
2.6239
2.6852
2.7472
2.8098
2.8731
2.9371
3.0017
3.0669
3.1329
3.1995
3.2668
3.3347
3.4034
3.4727
3.5427
3.6134
3.6847
3.7568
3.4237
3.5116
3.6005
3.6903
3.7812
3.8731
3.9659
4.0598
4.1547
4.2506
4.3475
4.4454
4.5443
4.6443
4.7453
4.8473
4.9503
5.0544
5.1596
5.2658
5.3730
5.4813
5.5907
5.7011
5.8126
1,536.7
1,576.1
1,616.0
1,656.3
1,697.1
1,738.4
1,780.0
1,822.2
1,864.8
1,907.8
1,951.3
1,995.2
2,039.6
2,084.5
2,129.8
2,175.6
2,221.9
2,268.6
2,315.8
2,363.4
2,411.6
2,460.2
2,509.3
2,558.8
2,608.9
0.51
0.52
0.53
0.54
1.4373
1.4845
1.5324
1.5809
2.2238
2.2969
2.3710
2.4461
998.1
1,030.9
1,064.2
1,097.9
0.91
0.92
0.93
0.94
3.8296
3.9030
3.9772
4.0521
5.9252
6.0389
6.1537
6.2695
2,659.4
2,710.4
2,762.0
2,814.0
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 42in
Palmer Bowlus Flume
0.95
4.1277
6.3865
2,866.5
1.35
7.7827
12.042
5,404.7
0.96
0.97
0.98
0.99
1.00
1.01
1.02
1.03
1.04
1.05
1.06
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
4.2040
4.2811
4.3588
4.4373
4.5165
4.5965
4.6772
4.7586
4.8408
4.9238
5.0075
5.0919
5.1771
5.2631
5.3499
5.4375
5.5258
5.6149
5.7048
5.7955
5.8870
5.9793
6.0724
6.1663
6.2611
6.3566
6.4530
6.5502
6.6483
6.7472
6.5046
6.6238
6.7441
6.8655
6.9881
7.1118
7.2367
7.3627
7.4898
7.6182
7.7477
7.8784
8.0102
8.1433
8.2775
8.4130
8.5497
8.6875
8.8266
8.9670
9.1085
9.2514
9.3954
9.541
9.687
9.835
9.984
10.135
10.286
10.439
2,919.5
2,973.0
3,027.0
3,081.5
3,136.5
3,192.0
3,248.0
3,304.6
3,361.7
3,419.3
3,477.4
3,536.1
3,595.2
3,655.0
3,715.2
3,776.0
3,837.3
3,899.2
3,961.7
4,024.7
4,088.2
4,152.3
4,217.0
4,282.2
4,348.0
4,414.3
4,481.3
4,548.8
4,616.9
4,685.5
1.36
1.37
1.38
1.39
1.40
1.41
1.42
1.43
1.44
1.45
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
1.54
1.55
1.56
1.57
1.58
1.59
1.60
1.61
1.62
1.63
1.64
1.65
7.8910
8.0002
8.1103
8.2212
8.3331
8.4458
8.5594
8.6740
8.7894
8.9057
9.0229
9.1410
9.2601
9.3800
9.5008
9.623
9.745
9.869
9.993
10.119
10.245
10.372
10.500
10.629
10.759
10.890
11.022
11.155
11.289
11.423
12.209
12.378
12.548
12.720
12.893
13.068
13.243
13.421
13.599
13.779
13.960
14.143
14.327
14.513
14.700
14.888
15.078
15.269
15.462
15.656
15.851
16.048
16.247
16.446
16.647
16.850
17.054
17.259
17.466
17.674
5,479.9
5,555.7
5,632.1
5,709.2
5,786.9
5,865.1
5,944.1
6,023.6
6,103.7
6,184.5
6,265.9
6,347.9
6,430.6
6,513.9
6,597.8
6,682.3
6,767.5
6,853.3
6,939.8
7,026.9
7,114.6
7,203.0
7,292.0
7,381.6
7,471.9
7,562.8
7,654.3
7,746.5
7,839.3
7,932.8
1.26
1.27
1.28
1.29
1.30
6.8469
6.9474
7.0488
7.1511
7.2542
10.594
10.749
10.906
11.064
11.224
4,754.8
4,824.6
4,895.0
4,966.0
5,037.6
1.66
1.67
1.68
1.69
1.70
11.559
11.695
11.832
11.971
12.110
17.884
18.095
18.307
18.521
18.737
8,026.8
8,121.6
8,216.9
8,312.9
8,409.5
1.31
1.32
1.33
1.34
7.3582
7.4630
7.5687
7.6753
11.385
11.547
11.711
11.875
5,109.8
5,182.6
5,256.0
5,330.0
1.71
1.72
1.73
1.74
12.250
12.391
12.533
12.675
18.953
19.171
19.391
19.612
8,506.8
8,604.7
8,703.2
8,802.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 42in
Palmer Bowlus Flume
1.75
12.819
19.834
8,902.1
2.16
19.429
30.061
13,492
1.76
1.77
1.78
1.79
1.80
12.964
13.109
13.255
13.403
13.551
20.058
20.283
20.509
20.737
20.966
9,002.5
9,103.5
9,205.1
9,307.4
9,410.2
2.17
2.18
2.19
2.20
2.21
19.606
19.783
19.961
20.140
20.319
30.334
30.609
30.885
31.161
31.438
13,615
13,738
13,862
13,986
14,111
1.81
1.82
1.83
1.84
1.85
1.86
1.87
1.88
1.89
1.90
1.91
1.92
1.93
1.94
1.95
13.700
13.850
14.000
14.152
14.304
14.458
14.612
14.767
14.923
15.080
15.237
15.396
15.555
15.715
15.876
21.197
21.428
21.662
21.896
22.132
22.369
22.608
22.848
23.089
23.332
23.576
23.821
24.067
24.315
24.563
9,513.7
9,617.8
9,722
9,828
9,934
10,040
10,147
10,255
10,363
10,472
10,581
10,691
10,802
10,913
11,025
2.22
2.23
2.24
2.25
2.26
2.27
2.28
2.29
2.30
2.31
2.32
2.33
2.34
2.35
2.36
20.499
20.680
20.861
21.042
21.224
21.407
21.590
21.774
21.958
22.143
22.328
22.514
22.700
22.887
23.074
31.717
31.996
32.276
32.557
32.839
33.121
33.405
33.689
33.974
34.260
34.547
34.834
35.122
35.411
35.700
14,235
14,361
14,486
14,613
14,739
14,866
14,993
15,121
15,249
15,377
15,506
15,635
15,764
15,893
16,023
1.96
1.97
1.98
1.99
2.00
16.037
16.200
16.363
16.527
16.692
24.814
25.065
25.318
25.571
25.826
11,137
11,250
11,363
11,477
11,592
2.37
2.38
2.39
2.40
2.41
23.261
23.449
23.638
23.826
24.016
35.991
36.281
36.573
36.865
37.158
16,154
16,284
16,415
16,546
16,678
2.01
2.02
2.03
2.04
2.05
16.858
17.024
17.191
17.359
17.528
26.083
26.340
26.599
26.858
27.119
11,707
11,822
11,938
12,055
12,172
2.06
2.07
2.08
2.09
2.10
2.11
17.697
17.867
18.038
18.209
18.381
18.554
27.381
27.644
27.909
28.174
28.440
28.708
12,290
12,408
12,526
12,645
12,765
12,885
2.12
2.13
2.14
2.15
18.728
18.902
19.077
19.253
28.976
29.246
29.517
29.788
13,005
13,126
13,248
13,370
2.42
24.205
37.451
16,809
2.43
24.395
37.745
16,941
2.44
24.586
38.040
17,073
2.45
24.776
38.335
17,206
*For points listed below please see footnote
1.
2.46
24.967
38.630
17,339
2.47
25.159
38.927
17,471
2.48
25.351
39.223
17,605
2.49
25.543
39.521
17,738
2.50
25.735
39.818
17,872
2.51
25.928
40.117
18,006
2.52
2.53
2.54
2.55
26.121
26.315
26.508
26.702
40.415
40.715
41.014
41.315
18,140
18,274
18,409
18,543
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 42in
Palmer Bowlus Flume
2.56
26.897
41.615
18,678
2.95
34.706
53.698
24,101
2.57
2.58
2.59
2.60
2.61
2.62
2.63
2.64
2.65
2.66
27.091
27.286
27.481
27.677
27.872
28.068
28.265
28.461
28.658
28.855
41.916
42.218
42.520
42.822
43.125
43.428
43.732
44.036
44.340
44.645
18,813
18,949
19,084
19,220
19,356
19,492
19,628
19,765
19,901
20,038
2.96
2.97
2.98
2.99
3.00
3.01
3.02
3.03
3.04
3.05
34.914
35.124
35.333
35.544
35.755
35.967
36.180
36.394
36.609
36.824
54.021
54.344
54.669
54.994
55.321
55.650
55.979
56.310
56.642
56.976
24,246
24,391
24,537
24,683
24,830
24,977
25,125
25,274
25,423
25,573
2.67
2.68
2.69
2.70
2.71
2.72
2.73
2.74
2.75
2.76
2.77
2.78
2.79
2.80
2.81
2.82
2.83
2.84
2.85
2.86
2.87
2.88
2.89
2.90
2.91
29.052
29.250
29.448
29.646
29.844
30.043
30.242
30.441
30.640
30.840
31.040
31.240
31.441
31.642
31.843
32.045
32.247
32.450
32.652
32.856
33.059
33.263
33.468
33.673
33.878
44.950
45.256
45.562
45.869
46.176
46.483
46.791
47.099
47.407
47.716
48.026
48.336
48.646
48.957
49.269
49.581
49.894
50.207
50.521
50.835
51.150
51.466
51.782
52.100
52.418
20,175
20,312
20,450
20,587
20,725
20,863
21,001
21,139
21,278
21,417
21,556
21,695
21,834
21,974
22,113
22,253
22,394
22,534
22,675
22,816
22,958
23,099
23,242
23,384
23,527
3.06
3.07
37.041
37.259
57.311
57.648
25,723
25,874
2.92
2.93
2.94
34.084
34.291
34.498
52.736
53.056
53.377
23,670
23,813
23,957
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 48in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.20
0.21
0.22
0.23
0.24
0.34376
0.37222
0.40154
0.43171
0.46273
0.53187
0.57590
0.62127
0.66795
0.71595
238.72
258.48
278.84
299.80
321.34
0.60
0.61
0.62
0.63
0.64
2.1001
2.1591
2.2188
2.2792
2.3403
3.2494
3.3407
3.4331
3.5265
3.6210
1,458.4
1,499.4
1,540.9
1,582.8
1,625.2
0.25
0.26
0.27
0.28
0.29
0.30
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.49459
0.52729
0.56081
0.59516
0.63032
0.66630
0.70308
0.74067
0.77905
0.81822
0.85817
0.89891
0.9404
0.9827
1.0258
0.76524
0.81583
0.86770
0.9208
0.9753
1.0309
1.0878
1.1460
1.2054
1.2660
1.3278
1.3908
1.4551
1.5205
1.5871
343.47
366.17
389.45
413.30
437.72
462.71
488.25
514.35
541.01
568.21
595.95
624.24
653.07
682.44
712.33
0.65
0.66
0.67
0.68
0.69
0.70
0.71
0.72
0.73
0.74
0.75
0.76
0.77
0.78
0.79
2.4021
2.4646
2.5278
2.5916
2.6562
2.7214
2.7874
2.8540
2.9213
2.9893
3.0579
3.1273
3.1973
3.2681
3.3395
3.7167
3.8133
3.9111
4.0099
4.1097
4.2107
4.3127
4.4157
4.5199
4.6251
4.7313
4.8386
4.9470
5.0565
5.1670
1,668.1
1,711.5
1,755.4
1,799.8
1,844.6
1,889.9
1,935.7
1,981.9
2,028.7
2,075.9
2,123.6
2,171.7
2,220.4
2,269.5
2,319.1
0.40
0.41
0.42
0.43
0.44
1.0696
1.1141
1.1595
1.2055
1.2524
1.6549
1.7238
1.7940
1.8652
1.9377
742.76
773.71
805.18
837.18
869.69
0.80
0.81
0.82
0.83
0.84
3.4116
3.4844
3.5579
3.6321
3.7070
5.2785
5.3912
5.5049
5.6197
5.7355
2,369.2
2,419.7
2,470.8
2,522.3
2,574.3
0.45
0.46
0.47
0.48
0.49
1.2999
1.3482
1.3972
1.4470
1.4975
2.0113
2.0860
2.1619
2.2389
2.3170
902.72
936.3
970.3
1,004.9
1,039.9
0.85
0.86
0.87
0.88
0.89
3.7825
3.8588
3.9358
4.0134
4.0918
5.8525
5.9705
6.0895
6.2097
6.3309
2,626.8
2,679.7
2,733.2
2,787.1
2,841.5
0.50
0.51
0.52
0.53
0.54
1.5487
1.6007
1.6533
1.7067
1.7608
2.3962
2.4766
2.5581
2.6406
2.7243
1,075.5
1,111.6
1,148.1
1,185.2
1,222.8
0.90
0.91
0.92
0.93
0.94
4.1709
4.2506
4.3311
4.4123
4.4942
6.4533
6.5767
6.7012
6.8268
6.9535
2,896.4
2,951.8
3,007.7
3,064.1
3,120.9
0.55
0.56
0.57
1.8156
1.8711
1.9273
2.8091
2.8950
2.9819
1,260.8
1,299.4
1,338.4
0.95
0.96
0.97
4.5768
4.6601
4.7441
7.0813
7.2102
7.3402
3,178.3
3,236.2
3,294.5
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 48in
Palmer Bowlus Flume
0.58
0.59
1.9842
2.0418
3.0700
3.1591
1,377.9
1,417.9
0.98
0.99
4.8289
4.9143
7.4714
7.6036
3,353.4
3,412.7
1.00
1.01
1.02
1.03
1.04
5.0005
5.0875
5.1751
5.2635
5.3527
7.7370
7.8715
8.0071
8.1439
8.2818
3,472.6
3,533.0
3,593.8
3,655.2
3,717.1
1.40
1.41
1.42
1.43
1.44
9.0822
9.2012
9.3211
9.4419
9.564
14.052
14.236
14.422
14.609
14.797
6,307.1
6,389.7
6,473.0
6,556.9
6,641.4
1.05
1.06
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
1.26
1.27
1.28
1.29
1.30
1.31
1.32
1.33
1.34
1.35
1.36
1.37
1.38
1.39
5.4425
5.5331
5.6245
5.7166
5.8094
5.9031
5.9974
6.0926
6.1885
6.2852
6.3826
6.4808
6.5798
6.6796
6.7802
6.8816
6.9838
7.0868
7.1905
7.2951
7.4005
7.5068
7.6138
7.7217
7.8304
7.9399
8.0503
8.1616
8.2736
8.3866
8.5003
8.6150
8.7305
8.8468
8.9641
8.4208
8.5610
8.7024
8.8449
8.9885
9.1334
9.2794
9.4266
9.575
9.725
9.875
10.027
10.181
10.335
10.491
10.647
10.805
10.965
11.125
11.287
11.450
11.615
11.780
11.947
12.115
12.285
12.456
12.628
12.801
12.976
13.152
13.329
13.508
13.688
13.870
3,779.5
3,842.4
3,905.9
3,969.9
4,034.3
4,099.3
4,164.9
4,231.0
4,297.6
4,364.7
4,432.4
4,500.6
4,569.3
4,638.6
4,708.5
4,778.9
4,849.8
4,921.4
4,993.4
5,066.1
5,139.3
5,213.0
5,287.4
5,362.3
5,437.8
5,513.8
5,590.5
5,667.7
5,745.6
5,824.0
5,903.0
5,982.6
6,062.8
6,143.6
6,225.1
1.45
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
1.54
1.55
1.56
1.57
1.58
1.59
1.60
1.61
1.62
1.63
1.64
1.65
1.66
1.67
1.68
1.69
1.70
1.71
1.72
1.73
1.74
1.75
1.76
1.77
1.78
1.79
9.686
9.810
9.934
10.059
10.185
10.313
10.441
10.570
10.699
10.830
10.962
11.095
11.228
11.363
11.498
11.635
11.772
11.911
12.050
12.190
12.331
12.474
12.617
12.761
12.906
13.052
13.199
13.347
13.496
13.647
13.798
13.950
14.103
14.256
14.411
14.987
15.178
15.370
15.564
15.759
15.956
16.154
16.353
16.554
16.757
16.961
17.166
17.373
17.581
17.791
18.002
18.214
18.428
18.644
18.861
19.080
19.300
19.521
19.744
19.969
20.195
20.422
20.652
20.882
21.114
21.348
21.583
21.820
22.058
22.298
6,726.5
6,812.2
6,898.6
6,985.6
7,073.2
7,161.5
7,250.4
7,339.9
7,430.1
7,521.0
7,612.5
7,704.6
7,797.4
7,890.9
7,985.0
8,079.7
8,175.2
8,271.2
8,368.0
8,465.4
8,563.5
8,662.3
8,761.7
8,861.8
8,962.6
9,064.1
9,166.2
9,269.0
9,372.6
9,476.7
9,581.6
9,687
9,793
9,900
10,008
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 48in
Palmer Bowlus Flume
1.80
1.81
1.82
1.83
1.84
1.85
1.86
1.87
1.88
1.89
14.567
14.724
14.882
15.041
15.201
15.362
15.524
15.687
15.851
16.015
22.539
22.782
23.026
23.272
23.520
23.768
24.019
24.271
24.525
24.780
10,116
10,225
10,335
10,445
10,556
10,668
10,780
10,894
11,007
11,122
2.20
2.21
2.22
2.23
2.24
2.25
2.26
2.27
2.28
2.29
21.607
21.802
21.998
22.195
22.393
22.592
22.792
22.992
23.194
23.396
33.431
33.733
34.037
34.341
34.648
34.955
35.264
35.574
35.886
36.198
15,005
15,140
15,277
15,414
15,551
15,689
15,828
15,967
16,107
16,247
1.90
1.91
1.92
1.93
1.94
1.95
1.96
1.97
1.98
1.99
2.00
2.01
2.02
2.03
2.04
2.05
2.06
2.07
2.08
2.09
2.10
2.11
2.12
2.13
2.14
16.181
16.348
16.516
16.685
16.855
17.025
17.197
17.370
17.544
17.718
17.894
18.071
18.248
18.427
18.606
18.787
18.968
19.151
19.334
19.518
19.704
19.890
20.077
20.265
20.454
25.036
25.294
25.554
25.815
26.078
26.342
26.608
26.875
27.144
27.414
27.686
27.959
28.234
28.511
28.788
29.068
29.348
29.631
29.914
30.200
30.486
30.774
31.064
31.355
31.647
11,237
11,353
11,469
11,587
11,705
11,823
11,942
12,062
12,183
12,304
12,426
12,549
12,672
12,796
12,921
13,046
13,172
13,299
13,427
13,554
13,683
13,812
13,942
14,073
14,204
2.30
2.31
2.32
2.33
2.34
2.35
2.36
2.37
2.38
2.39
2.40
2.41
2.42
2.43
2.44
2.45
2.46
2.47
2.48
2.49
2.50
2.51
2.52
2.53
2.54
23.599
23.802
24.007
24.212
24.419
24.626
24.833
25.042
25.251
25.461
25.672
25.883
26.096
26.309
26.522
26.737
26.952
27.168
27.384
27.601
27.819
28.037
28.256
28.476
28.696
36.513
36.828
37.144
37.462
37.781
38.101
38.423
38.745
39.069
39.394
39.720
40.048
40.376
40.706
41.036
41.368
41.701
42.034
42.369
42.705
43.042
43.380
43.719
44.058
44.399
16,388
16,529
16,672
16,814
16,957
17,101
17,245
17,390
17,536
17,681
17,828
17,975
18,122
18,270
18,418
18,567
18,716
18,866
19,017
19,167
19,319
19,470
19,622
19,775
19,928
2.15
2.16
2.17
2.18
2.19
20.644
20.835
21.026
21.219
21.413
31.941
32.236
32.533
32.831
33.130
14,336
14,469
14,602
14,735
14,870
2.55
2.56
2.57
2.58
2.59
28.917
29.138
29.360
29.583
29.806
44.741
45.083
45.427
45.771
46.117
20,081
20,235
20,389
20,544
20,699
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 48in
Palmer Bowlus Flume
2.60
2.61
2.62
2.63
2.64
2.65
2.66
2.67
2.68
2.69
30.030
30.254
30.479
30.704
30.930
31.156
31.383
31.610
31.838
32.066
46.463
46.810
47.157
47.506
47.855
48.206
48.556
48.908
49.261
49.614
20,854
21,010
21,166
21,322
21,479
21,636
21,794
21,951
22,110
22,268
3.00
3.01
3.02
3.03
3.04
3.05
3.06
3.07
3.08
3.09
39.330
39.569
39.809
40.049
40.289
40.529
40.770
41.011
41.253
41.494
60.852
61.222
61.593
61.964
62.336
62.708
63.081
63.454
63.827
64.201
27,312
27,478
27,645
27,811
27,978
28,145
28,313
28,480
28,648
28,815
2.70
2.71
2.72
2.73
2.74
2.75
2.76
2.77
2.78
2.79
32.295
32.524
32.754
32.984
33.214
33.445
33.676
33.908
34.140
34.372
49.968
50.322
50.677
51.033
51.390
51.747
52.105
52.463
52.822
53.182
22,427
22,586
22,746
22,905
23,065
23,226
23,386
23,547
23,708
23,870
3.10
3.11
3.12
3.13
3.14
3.15
3.16
3.17
3.18
3.19
41.736
41.979
42.221
42.464
42.708
42.952
43.196
43.440
43.685
43.930
64.576
64.951
65.326
65.702
66.079
66.456
66.834
67.212
67.591
67.970
28,984
29,152
29,320
29,489
29,658
29,827
29,997
30,167
30,337
30,507
3.20
3.21
3.22
3.23
3.24
3.25
3.26
3.27
3.28
3.29
3.30
3.31
3.32
3.33
3.34
3.35
44.176
44.422
44.669
44.916
45.164
45.412
45.660
45.910
46.159
46.410
46.661
46.913
47.165
47.418
47.672
47.927
68.350
68.731
69.113
69.495
69.878
70.262
70.647
71.033
71.419
71.807
72.195
72.585
72.975
73.367
73.760
74.154
30,678
30,849
31,020
31,192
31,364
31,536
31,709
31,882
32,055
32,229
32,403
32,578
32,754
32,929
33,106
33,283
3.36
3.37
3.38
3.39
48.183
48.439
48.696
48.955
74.549
74.946
75.344
75.744
33,460
33,638
33,817
33,996
2.80
34.605
53.542
24,031
*For points listed below please see footnote 1.
2.81
34.838
53.903
24,193
2.82
35.072
54.264
24,355
2.83
35.306
54.626
24,518
2.84
35.540
54.988
24,680
2.85
35.774
55.351
24,843
2.86
36.009
55.715
25,006
2.87
36.244
56.078
25,170
2.88
36.480
56.443
25,333
2.89
36.716
56.808
25,497
2.90
36.952
57.173
25,661
2.91
37.188
57.539
25,825
2.92
37.425
57.905
25,990
2.93
37.662
58.272
26,154
2.94
37.900
58.639
26,319
2.95
2.96
2.97
2.98
2.99
38.137
38.375
38.613
38.852
39.091
59.007
59.375
59.744
60.113
60.482
26,484
26,649
26,815
26,980
27,146
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 54in
Palmer Bowlus Flume
(feet)
0.23
0.24
0.25
0.26
0.27
0.28
0.29
MGD
0.49652
0.52752
0.55942
0.59223
0.62596
0.6606
0.6961
CFS
0.7682
0.8162
0.8656
0.9163
0.9685
1.0221
1.0771
GPM
344.81
366.33
388.49
411.27
434.69
458.74
483.41
(feet)
MGD
CFS
GPM
0.65
0.66
0.67
0.68
0.69
2.5689
2.6372
2.7064
2.7764
2.8473
3.9747
4.0803
4.1874
4.2957
4.4054
1,783.9
1,831.4
1,879.4
1,928.1
1,977.3
0.30
0.31
0.32
0.33
0.34
0.7326
0.7699
0.8081
0.8473
0.8873
1.1334
1.1912
1.2504
1.3109
1.3729
508.72
534.65
561.20
588.39
616.19
0.70
0.71
0.72
0.73
0.74
2.9191
2.9917
3.0652
3.1396
3.2149
4.5165
4.6289
4.7426
4.8577
4.9741
2,027.1
2,077.6
2,128.6
2,180.3
2,232.5
0.35
0.36
0.37
0.38
0.39
0.9283
0.9701
1.0128
1.0564
1.1010
1.4362
1.5009
1.5671
1.6346
1.7034
644.62
673.7
703.3
733.6
764.6
0.75
0.76
0.77
0.78
0.79
3.2910
3.3680
3.4458
3.5245
3.6041
5.0919
5.2110
5.3314
5.4532
5.5763
2,285.4
2,338.9
2,392.9
2,447.6
2,502.8
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
0.49
0.50
0.51
0.52
0.53
0.54
0.55
0.56
0.57
0.58
0.59
1.1464
1.1927
1.2399
1.2879
1.3369
1.3868
1.4375
1.4891
1.5416
1.5950
1.6493
1.7045
1.7605
1.8174
1.8752
1.9339
1.9935
2.0539
2.1152
2.1774
1.7737
1.8453
1.9183
1.9927
2.0685
2.1456
2.2241
2.3040
2.3853
2.4679
2.5519
2.6372
2.7239
2.8120
2.9014
2.9922
3.0844
3.1779
3.2727
3.3689
796.1
828.2
861.0
894.4
928.4
963.0
998.3
1,034.1
1,070.6
1,107.7
1,145.4
1,183.7
1,222.6
1,262.1
1,302.2
1,343.0
1,384.4
1,426.3
1,468.9
1,512.1
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
0.90
0.91
0.92
0.93
0.94
0.95
0.96
0.97
0.98
0.99
3.6845
3.7658
3.8479
3.9310
4.0148
4.0996
4.1852
4.2716
4.3589
4.4471
4.5361
4.6260
4.7168
4.8084
4.9008
4.9941
5.0883
5.1833
5.2792
5.3759
5.7008
5.8265
5.9536
6.0821
6.2119
6.3430
6.4754
6.6092
6.7443
6.8807
7.0184
7.1575
7.2979
7.4396
7.5827
7.7271
7.8727
8.0198
8.1681
8.3178
2,558.7
2,615.1
2,672.2
2,729.8
2,788.1
2,846.9
2,906.4
2,966.4
3,027.0
3,088.3
3,150.1
3,212.5
3,275.5
3,339.1
3,403.3
3,468.1
3,533.5
3,599.5
3,666.1
3,733.3
0.60
0.61
0.62
2.2405
2.3044
2.3692
3.4665
3.5654
3.6657
1,555.9
1,600.3
1,645.3
1.00
1.01
1.02
5.4735
5.5719
5.6712
8.4687
8.6210
8.7747
3,801.0
3,869.4
3,938.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 54in
Palmer Bowlus Flume
0.63
0.64
2.4349
2.5015
3.7674
3.8703
1,690.9
1,737.1
1.03
1.04
5.7713
5.8723
8.9296
9.0858
4,007.9
4,078.0
1.05
1.06
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
1.26
1.27
1.28
1.29
1.30
1.31
1.32
1.33
1.34
1.35
1.36
1.37
1.38
1.39
5.9742
6.0769
6.1804
6.2848
6.3900
6.4961
6.6030
6.7108
6.8195
6.9289
7.0393
7.1504
7.2625
7.3753
7.4890
7.6036
7.7190
7.8352
7.9523
8.0703
8.1890
8.3086
8.429
8.550
8.673
8.796
8.919
9.044
9.170
9.296
9.423
9.551
9.680
9.810
9.940
9.2434
9.4023
9.5625
9.7240
9.8868
10.0510
10.2164
10.3832
10.5513
10.7207
10.8914
11.0634
11.2367
11.4113
11.5872
11.7645
11.9430
12.1229
12.3041
12.4865
12.6703
12.8554
13.0418
13.2294
13.4184
13.6087
13.8003
13.9932
14.1874
14.3829
14.5797
14.7778
14.9771
15.1778
15.3798
4,148.7
4,220.0
4,291.9
4,364.4
4,437.5
4,511.2
4,585.4
4,660.3
4,735.7
4,811.8
4,888.4
4,965.6
5,043.4
5,121.8
5,200.7
5,280.3
5,360.4
5,441.1
5,522.4
5,604.3
5,686.8
5,769.9
5,853.5
5,937.8
6,022.6
6,108.0
6,194.0
6,280.6
6,367.7
6,455.5
6,543.8
6,632.7
6,722.2
6,812.3
6,902.9
1.45
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
1.54
1.55
1.56
1.57
1.58
1.59
1.60
1.61
1.62
1.63
1.64
1.65
1.66
1.67
1.68
1.69
1.70
1.71
1.72
1.73
1.74
1.75
1.76
1.77
1.78
1.79
10.741
10.878
11.015
11.153
11.292
11.432
11.572
11.714
11.856
11.999
12.143
12.288
12.433
12.580
12.727
12.875
13.024
13.174
13.324
13.476
13.628
13.781
13.935
14.090
14.245
14.402
14.559
14.717
14.876
15.035
15.196
15.357
15.520
15.683
15.846
16.6190
16.8300
17.0424
17.2560
17.4709
17.6872
17.9047
18.1235
18.3436
18.5650
18.7877
19.0116
19.2369
19.4635
19.6913
19.9204
20.1508
20.3825
20.6155
20.8498
21.0854
21.3222
21.5603
21.7998
22.0405
22.2824
22.5257
22.7703
23.0161
23.2632
23.5116
23.7613
24.0123
24.2645
24.5180
7,459.1
7,553.8
7,649.1
7,745.0
7,841.5
7,938.5
8,036.2
8,134.4
8,233.2
8,332.5
8,432.5
8,533.0
8,634.1
8,736
8,838
8,941
9,044
9,148
9,253
9,358
9,464
9,570
9,677
9,784
9,892
10,001
10,110
10,220
10,330
10,441
10,553
10,665
10,777
10,891
11,004
1.40
1.41
1.42
1.43
10.072
10.204
10.337
10.471
15.5831
15.7877
15.9936
16.2007
6,994.2
7,086.0
7,178.4
7,271.4
1.80
1.81
1.82
1.83
16.011
16.177
16.343
16.510
24.7728
25.0289
25.2863
25.5449
11,119
11,234
11,349
11,465
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 54in
Palmer Bowlus Flume
1.44
10.606
16.4092
7,365.0
1.84
16.678
25.8049
11,582
1.85
1.86
1.87
1.88
1.89
16.847
17.017
17.187
17.358
17.530
26.0661
26.3285
26.5923
26.8573
27.1236
11,699
11,817
11,935
12,054
12,174
2.25
2.26
2.27
2.28
2.29
24.275
24.477
24.680
24.884
25.089
37.5582
37.8716
38.1861
38.5020
38.8191
16,857
16,998
17,139
17,281
17,423
1.90
1.91
1.92
1.93
1.94
1.95
1.96
1.97
1.98
1.99
2.00
2.01
2.02
2.03
2.04
2.05
2.06
2.07
2.08
2.09
2.10
2.11
2.12
2.13
2.14
2.15
2.16
2.17
2.18
2.19
17.703
17.877
18.052
18.227
18.403
18.580
18.758
18.937
19.117
19.297
19.478
19.660
19.843
20.027
20.211
20.396
20.583
20.769
20.957
21.146
21.335
21.525
21.716
21.908
22.101
22.295
22.489
22.684
22.880
23.077
27.3912
27.6601
27.9302
28.2016
28.4743
28.7483
29.0235
29.3000
29.5778
29.8569
30.1372
30.4188
30.7017
30.9858
31.2712
31.5579
31.8459
32.1351
32.4256
32.7174
33.0104
33.3048
33.6003
33.8972
34.1953
34.4947
34.7954
35.0973
35.4005
35.7049
12,294
12,415
12,536
12,658
12,780
12,903
13,027
13,151
13,275
13,401
13,527
13,653
13,780
13,907
14,036
14,164
14,293
14,423
14,554
14,685
14,816
14,948
15,081
15,214
15,348
15,482
15,617
15,753
15,889
16,025
2.30
2.31
2.32
2.33
2.34
2.35
2.36
2.37
2.38
2.39
2.40
2.41
2.42
2.43
2.44
2.45
2.46
2.47
2.48
2.49
2.50
2.51
2.52
2.53
2.54
2.55
2.56
2.57
2.58
2.59
25.295
25.502
25.709
25.917
26.126
26.336
26.547
26.758
26.971
27.184
27.398
27.613
27.828
28.044
28.262
28.480
28.698
28.918
29.139
29.360
29.582
29.805
30.028
30.253
30.478
30.704
30.931
31.159
31.388
31.617
39.1375
39.4571
39.7780
40.1002
40.4236
40.7483
41.0742
41.4014
41.7299
42.0596
42.3906
42.7229
43.0564
43.3912
43.7272
44.0645
44.4030
44.7429
45.0839
45.4263
45.7698
46.1147
46.4608
46.8081
47.1568
47.5066
47.8578
48.2101
48.5638
48.9187
17,566
17,710
17,854
17,998
18,143
18,289
18,435
18,582
18,730
18,878
19,026
19,175
19,325
19,475
19,626
19,778
19,929
20,082
20,235
20,389
20,543
20,698
20,853
21,009
21,165
21,322
21,480
21,638
21,797
21,956
2.20
2.21
2.22
2.23
2.24
23.274
23.473
23.672
23.872
24.073
36.0106
36.3176
36.6259
36.9354
37.2462
16,163
16,300
16,439
16,578
16,717
2.60
2.61
2.62
2.63
31.847
32.078
32.310
32.543
49.2748
49.6322
49.9909
50.3508
22,116
22,276
22,437
22,599
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 54in
Palmer Bowlus Flume
2.64
2.65
2.66
2.67
2.68
2.69
2.70
2.71
2.72
2.73
2.74
2.75
2.76
2.77
2.78
2.79
2.80
2.81
2.82
2.83
2.84
2.85
2.86
2.87
2.88
2.89
2.90
2.91
2.92
2.93
2.94
2.95
2.96
2.97
2.98
2.99
32.776
33.010
33.245
33.481
33.718
33.955
34.194
34.433
34.673
34.913
35.155
35.397
35.640
35.884
36.129
36.375
36.621
36.868
37.116
37.365
37.615
37.865
38.116
38.368
38.621
38.875
39.129
39.384
39.641
39.897
40.155
40.414
40.673
40.933
41.194
41.456
50.7120
51.0744
51.4381
51.8030
52.1692
52.5366
52.9053
53.2753
53.6465
54.0189
54.3926
54.7676
55.1438
55.5212
55.8999
56.2799
56.6611
57.0435
57.4272
57.8122
58.1984
58.5858
58.9745
59.3645
59.7557
60.1481
60.5418
60.9368
61.3330
61.7304
62.1291
62.5290
62.9302
63.3326
63.7363
64.1412
22,761
22,924
23,087
23,251
23,415
23,580
23,746
23,912
24,078
24,245
24,413
24,581
24,750
24,920
25,090
25,260
25,431
25,603
25,775
25,948
26,121
26,295
26,470
26,645
26,820
26,996
27,173
27,350
27,528
27,707
27,885
28,065
28,245
28,426
28,607
28,789
3.00
3.01
3.02
3.03
3.04
41.718
41.981
42.246
42.510
42.776
64.5474
64.9548
65.3635
65.7734
66.1845
28,971
29,154
29,337
29,521
29,706
3.05
43.043
66.5969
29,891
3.06
43.310
67.0105
30,076
3.07
43.578
67.4254
30,263
3.08
43.847
67.8415
30,449
3.09
44.117
68.2589
30,637
3.10
44.387
68.6775
30,825
3.11
44.659
69.0974
31,013
3.12
44.931
69.5185
31,202
3.13
45.204
69.9408
31,392
3.14
45.478
70.3644
31,582
*For points listed below please see footnote 1.
3.15
45.752
70.7892
31,772
3.16
46.028
71.2153
31,964
3.17
46.304
71.6426
32,155
3.18
46.581
72.0711
32,348
3.19
46.859
72.5009
32,541
3.20
47.137
72.9320
32,734
3.21
47.417
73.3642
32,928
3.22
47.697
73.7978
33,123
3.23
47.978
74.2325
33,318
3.24
48.260
74.6685
33,514
3.25
48.542
75.1058
33,710
3.26
48.826
75.5442
33,907
3.27
49.110
75.9840
34,104
3.28
49.395
76.4249
34,302
3.29
49.681
76.8671
34,500
3.30
49.967
77.3105
34,699
3.31
50.255
77.7552
34,899
3.32
50.543
78.2011
35,099
3.33
50.832
78.6483
35,300
3.34
51.122
79.0967
35,501
3.35
51.412
79.5463
35,703
3.36
51.704
79.9972
35,905
3.37
51.996
80.4493
36,108
3.38
52.289
80.9026
36,312
3.39
52.583
81.3572
36,516
3.40
3.41
3.42
3.43
3.44
52.877
53.173
53.469
53.766
54.064
81.8131
82.2701
82.7284
83.1879
83.6487
36,720
36,925
37,131
37,337
37,544
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 54in
Palmer Bowlus Flume
3.45
3.46
3.47
3.48
3.49
3.50
3.51
3.52
3.53
3.54
54.362
54.662
54.962
55.263
55.565
55.867
56.171
56.475
56.780
57.086
84.1107
84.5740
85.0384
85.5041
85.9711
86.4393
86.9087
87.3794
87.8512
88.3244
37,751
37,959
38,168
38,377
38,586
38,797
39,007
39,219
39,430
39,643
3.85
3.86
3.87
3.88
3.89
3.90
3.91
3.92
3.93
3.94
66.960
67.291
67.624
67.956
68.290
68.624
68.960
69.296
69.633
69.970
103.6027
104.1152
104.6290
105.1440
105.6602
106.1777
106.6964
107.2163
107.7374
108.2598
46,500
46,730
46,961
47,192
47,424
47,656
47,889
48,122
48,356
48,590
3.55
3.56
3.57
3.58
3.59
57.392
57.700
58.008
58.317
58.626
88.7987
89.2743
89.7512
90.2292
90.7085
39,856
40,069
40,283
40,498
40,713
3.95
3.96
3.97
3.98
3.99
70.309
70.648
70.988
71.329
71.670
108.7834
109.3082
109.8343
110.3615
110.8900
48,825
49,061
49,297
49,534
49,771
3.60
3.61
3.62
3.63
3.64
3.65
3.66
3.67
3.68
3.69
58.937
59.248
59.561
59.874
60.187
60.502
60.817
61.133
61.450
61.768
91.1890
91.6708
92.1538
92.6380
93.1235
93.6102
94.0981
94.5873
95.0777
95.5693
40,928
41,145
41,361
41,579
41,797
42,015
42,234
42,454
42,674
42,894
4.00
4.01
4.02
4.03
4.04
4.05
4.06
4.07
4.08
4.09
72.012
72.356
72.700
73.044
73.390
73.736
74.083
74.431
74.780
75.130
111.4198
111.9507
112.4829
113.0163
113.5510
114.0868
114.6239
115.1622
115.7017
116.2425
50,009
50,247
50,486
50,725
50,965
51,206
51,447
51,688
51,931
52,173
3.70
3.71
3.72
3.73
3.74
3.75
3.76
3.77
3.78
3.79
3.80
3.81
3.82
3.83
3.84
62.087
62.406
62.726
63.047
63.369
63.691
64.015
64.339
64.664
64.989
65.316
65.643
65.971
66.300
66.630
96.0622
96.5562
97.0516
97.5481
98.0459
98.5449
99.0452
99.5466
100.0493
100.5533
101.0584
101.5648
102.0724
102.5813
103.0914
43,116
43,337
43,560
43,783
44,006
44,230
44,455
44,680
44,905
45,131
45,358
45,585
45,813
46,042
46,271
4.10
4.11
4.12
4.13
4.14
4.15
4.16
4.17
4.18
4.19
4.20
75.480
75.831
76.183
76.535
76.889
77.243
77.598
77.954
78.311
78.668
79.026
116.7845
117.3277
117.8721
118.4178
118.9647
119.5128
120.0621
120.6127
121.1645
121.7175
122.2717
52,417
52,660
52,905
53,150
53,395
53,641
53,888
54,135
54,382
54,631
54,879
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
5
Flow Chart for 60in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
0.25
0.26
0.27
0.28
0.29
0.50575
0.55204
0.59909
0.6469
0.6954
0.7825
0.8541
0.9269
1.0009
1.0760
351.21
383.36
416.04
449.23
482.94
0.65
0.66
0.67
0.68
0.69
2.9245
2.9995
3.0752
3.1517
3.2288
4.5248
4.6409
4.7581
4.8763
4.9957
2,030.9
2,083.0
2,135.6
2,188.6
2,242.2
0.30
0.31
0.32
0.33
0.34
0.7447
0.7948
0.8455
0.8970
0.9493
1.1523
1.2297
1.3082
1.3879
1.4688
517.17
551.92
587.17
622.95
659.23
0.70
0.71
0.72
0.73
0.74
3.3066
3.3852
3.4644
3.5444
3.6251
5.1161
5.2376
5.3603
5.4840
5.6088
2,296.3
2,350.8
2,405.9
2,461.4
2,517.4
0.35
0.36
0.37
0.38
0.39
1.0023
1.0560
1.1104
1.1656
1.2215
1.5507
1.6338
1.7181
1.8034
1.8899
696.02
733.3
771.1
809.4
848.2
0.75
0.76
0.77
0.78
0.79
3.7064
3.7885
3.8713
3.9548
4.0391
5.7347
5.8617
5.9898
6.1191
6.2494
2,573.9
2,630.9
2,688.4
2,746.4
2,804.9
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
0.49
0.50
0.51
0.52
0.53
0.54
0.55
0.56
0.57
0.58
0.59
0.60
0.61
0.62
0.63
0.64
1.2781
1.3354
1.3935
1.4522
1.5117
1.5719
1.6328
1.6944
1.7568
1.8198
1.8836
1.9480
2.0132
2.0791
2.1457
2.2129
2.2809
2.3496
2.4190
2.4891
2.5599
2.6314
2.7036
2.7765
2.8502
1.9775
2.0662
2.1560
2.2469
2.3390
2.4321
2.5263
2.6217
2.7181
2.8157
2.9143
3.0141
3.1149
3.2168
3.3198
3.4239
3.5291
3.6354
3.7428
3.8512
3.9608
4.0714
4.1831
4.2959
4.4098
887.6
927.4
967.7
1,008.5
1,049.8
1,091.6
1,133.9
1,176.7
1,220.0
1,263.8
1,308.0
1,352.8
1,398.1
1,443.8
1,490.0
1,536.8
1,584.0
1,631.7
1,679.9
1,728.6
1,777.7
1,827.4
1,877.5
1,928.2
1,979.3
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
0.90
0.91
0.92
0.93
0.94
0.95
0.96
0.97
0.98
0.99
1.00
1.01
1.02
1.03
1.04
4.1240
4.2097
4.2961
4.3832
4.4710
4.5595
4.6488
4.7388
4.8296
4.9210
5.0132
5.1061
5.1998
5.2942
5.3894
5.4852
5.5819
5.6793
5.7774
5.8763
5.9759
6.0763
6.1775
6.2794
6.3821
6.3808
6.5134
6.6470
6.7818
6.9177
7.0547
7.1928
7.3320
7.4724
7.6139
7.7566
7.9004
8.0453
8.1913
8.3386
8.4869
8.6364
8.787
8.939
9.092
9.246
9.401
9.558
9.716
9.875
2,863.9
2,923.4
2,983.4
3,043.9
3,104.9
3,166.4
3,228.3
3,290.8
3,353.9
3,417.4
3,481.4
3,545.9
3,611.0
3,676.5
3,742.6
3,809.2
3,876.3
3,943.9
4,012.1
4,080.8
4,150.0
4,219.7
4,289.9
4,360.7
4,432.0
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 60in
Palmer Bowlus Flume
1.05
1.06
1.07
1.08
1.09
6.4856
6.5899
6.6949
6.8007
6.9072
10.035
10.196
10.358
10.522
10.687
4,503.9
4,576.3
4,649.2
4,722.7
4,796.7
1.45
1.46
1.47
1.48
1.49
11.292
11.430
11.569
11.709
11.849
17.472
17.685
17.900
18.116
18.334
7,841.9
7,937.7
8,034.1
8,131.1
8,228.7
1.10
1.11
1.12
1.13
1.14
7.0146
7.1228
7.2317
7.3414
7.4520
10.853
11.021
11.189
11.359
11.530
4,871.2
4,946.4
5,022.0
5,098.2
5,175.0
1.50
1.51
1.52
1.53
1.54
11.991
12.133
12.277
12.421
12.566
18.553
18.773
18.995
19.218
19.443
8,327.0
8,426.0
8,525.6
8,625.8
8,726.7
1.15
1.16
1.17
1.18
1.19
7.5633
7.6754
7.7884
7.9021
8.0167
11.702
11.876
12.050
12.226
12.404
5,252.3
5,330.2
5,408.6
5,487.6
5,567.1
1.55
1.56
1.57
1.58
1.59
12.713
12.860
13.008
13.157
13.307
19.669
19.897
20.126
20.357
20.589
8,828.2
8,930.5
9,033.3
9,137
9,241
1.20
1.21
1.22
1.23
1.24
8.1321
8.2483
8.3653
8.4831
8.6018
12.582
12.762
12.943
13.125
13.309
5,647.3
5,728.0
5,809.2
5,891.1
5,973.5
1.60
1.61
1.62
1.63
1.64
13.458
13.610
13.763
13.917
14.072
20.823
21.058
21.295
21.533
21.772
9,346
9,451
9,558
9,665
9,772
1.25
1.26
1.27
1.28
1.29
8.7213
8.8417
8.963
9.085
9.208
13.494
13.680
13.868
14.056
14.247
6,056.5
6,140.1
6,224.2
6,309.0
6,394.3
1.65
1.66
1.67
1.68
1.69
14.228
14.384
14.542
14.701
14.861
22.013
22.256
22.500
22.746
22.993
9,880
9,989
10,099
10,209
10,320
1.30
1.31
1.32
1.33
1.34
1.35
1.36
1.37
1.38
1.39
1.40
1.41
1.42
1.43
1.44
9.332
9.456
9.582
9.708
9.835
9.963
10.092
10.222
10.353
10.484
10.617
10.750
10.884
11.019
11.155
14.438
14.631
14.825
15.020
15.217
15.415
15.615
15.816
16.018
16.221
16.426
16.633
16.840
17.050
17.260
6,480.3
6,566.8
6,653.9
6,741.6
6,829.9
6,918.9
7,008.4
7,098.5
7,189.3
7,280.7
7,372.7
7,465.3
7,558.5
7,652.4
7,746.8
1.70
1.71
1.72
1.73
1.74
1.75
1.76
1.77
1.78
1.79
1.80
1.81
1.82
1.83
1.84
15.022
15.184
15.346
15.510
15.675
15.841
16.008
16.175
16.344
16.514
16.685
16.857
17.030
17.204
17.379
23.242
23.492
23.744
23.998
24.253
24.509
24.767
25.027
25.288
25.551
25.816
26.082
26.349
26.618
26.889
10,432
10,544
10,657
10,771
10,885
11,001
11,116
11,233
11,350
11,468
11,587
11,706
11,826
11,947
12,069
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 60in
Palmer Bowlus Flume
1.85
1.86
1.87
1.88
1.89
17.555
17.732
17.910
18.090
18.270
27.162
27.436
27.711
27.989
28.268
12,191
12,314
12,438
12,562
12,687
2.25
2.26
2.27
2.28
2.29
25.471
25.691
25.912
26.134
26.357
39.409
39.750
40.092
40.435
40.781
17,688
17,841
17,994
18,149
18,304
1.90
1.91
1.92
1.93
1.94
18.451
18.633
18.817
19.001
19.187
28.548
28.830
29.114
29.399
29.686
12,813
12,940
13,067
13,195
13,324
2.30
2.31
2.32
2.33
2.34
26.582
26.807
27.034
27.262
27.490
41.128
41.477
41.828
42.180
42.534
18,460
18,616
18,774
18,932
19,090
1.95
1.96
1.97
1.98
1.99
2.00
2.01
2.02
2.03
2.04
19.373
19.561
19.750
19.939
20.130
20.322
20.515
20.709
20.904
21.101
29.975
30.265
30.557
30.851
31.146
31.443
31.742
32.042
32.344
32.647
13,454
13,584
13,715
13,847
13,979
14,113
14,247
14,381
14,517
14,653
2.35
2.36
2.37
2.38
2.39
2.40
2.41
2.42
2.43
2.44
27.720
27.951
28.183
28.416
28.650
28.885
29.122
29.359
29.597
29.837
42.889
43.247
43.605
43.966
44.328
44.692
45.058
45.425
45.794
46.164
19,250
19,410
19,571
19,733
19,896
20,059
20,223
20,388
20,554
20,720
2.05
2.06
2.07
2.08
2.09
2.10
2.11
2.12
2.13
2.14
21.298
21.496
21.696
21.896
22.098
22.300
22.504
22.709
22.915
23.122
32.953
33.260
33.568
33.878
34.190
34.504
34.819
35.136
35.455
35.775
14,790
14,928
15,066
15,206
15,346
15,486
15,628
15,770
15,913
16,057
2.45
2.46
2.47
2.48
2.49
2.50
2.51
2.52
2.53
2.54
30.077
30.319
30.562
30.805
31.050
31.296
31.543
31.791
32.040
32.290
46.536
46.910
47.286
47.663
48.041
48.422
48.804
49.187
49.573
49.959
20,887
21,055
21,223
21,393
21,562
21,733
21,905
22,077
22,250
22,423
2.15
2.16
2.17
2.18
2.19
2.20
2.21
2.22
2.23
2.24
23.330
23.539
23.749
23.961
24.173
24.387
24.601
24.817
25.034
25.252
36.097
36.421
36.746
37.073
37.402
37.732
38.064
38.398
38.733
39.070
16,201
16,347
16,493
16,639
16,787
16,935
17,084
17,234
17,385
17,536
2.55
2.56
2.57
2.58
2.59
2.60
2.61
2.62
2.63
2.64
32.541
32.793
33.046
33.300
33.555
33.811
34.069
34.327
34.586
34.846
50.348
50.738
51.130
51.523
51.918
52.314
52.712
53.112
53.513
53.915
22,598
22,773
22,949
23,125
23,302
23,480
23,659
23,838
24,018
24,199
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 60in
Palmer Bowlus Flume
2.65
2.66
2.67
2.68
2.69
2.70
2.71
2.72
2.73
2.74
2.75
2.76
2.77
2.78
2.79
2.80
2.81
2.82
2.83
2.84
2.85
2.86
2.87
2.88
2.89
2.90
35.108
35.370
35.633
35.898
36.163
36.429
36.696
36.965
37.234
37.504
37.775
38.047
38.320
38.594
38.869
39.145
39.422
39.700
39.978
40.258
40.539
40.820
41.102
41.386
41.670
41.955
54.320
54.726
55.133
55.542
55.952
56.364
56.778
57.193
57.609
58.027
58.447
58.868
59.290
59.714
60.140
60.566
60.995
61.425
61.856
62.288
62.722
63.158
63.595
64.033
64.473
64.914
24,380
24,563
24,745
24,929
25,113
25,298
25,484
25,670
25,857
26,044
26,233
26,422
26,611
26,802
26,993
27,184
27,376
27,569
27,763
27,957
28,152
28,347
28,543
28,740
28,937
29,135
3.05
3.06
3.07
3.08
3.09
3.10
3.11
3.12
3.13
3.14
3.15
3.16
3.17
3.18
3.19
3.20
3.21
3.22
3.23
3.24
3.25
3.26
3.27
3.28
3.29
3.30
46.333
46.631
46.930
47.230
47.531
47.833
48.135
48.438
48.742
49.046
49.352
49.658
49.964
50.272
50.580
50.888
51.198
51.508
51.819
52.130
52.443
52.755
53.069
53.383
53.698
54.013
71.687
72.149
72.612
73.076
73.542
74.008
74.476
74.945
75.415
75.886
76.358
76.832
77.306
77.782
78.258
78.736
79.215
79.695
80.176
80.658
81.141
81.624
82.109
82.595
83.082
83.570
32,176
32,383
32,591
32,799
33,008
33,217
33,427
33,638
33,848
34,060
34,272
34,484
34,697
34,911
35,125
35,339
35,554
35,769
35,985
36,202
36,418
36,636
36,853
37,071
37,290
37,509
2.91
2.92
2.93
2.94
2.95
2.96
2.97
2.98
2.99
3.00
3.01
3.02
3.03
3.04
42.241
42.527
42.815
43.104
43.393
43.683
43.974
44.266
44.559
44.853
45.147
45.442
45.738
46.035
65.356
65.800
66.245
66.691
67.139
67.588
68.038
68.490
68.943
69.397
69.853
70.310
70.768
71.227
29,334
29,533
29,733
29,933
30,134
30,336
30,538
30,740
30,944
31,148
31,352
31,557
31,763
31,969
3.31
3.32
3.33
3.34
3.35
3.36
3.37
3.38
3.39
3.40
3.41
3.42
3.43
3.44
54.329
54.645
54.962
55.280
55.599
55.917
56.237
56.557
56.878
57.199
57.520
57.843
58.165
58.489
84.059
84.549
85.039
85.531
86.024
86.517
87.011
87.506
88.002
88.499
88.997
89.496
89.995
90.495
37,728
37,948
38,168
38,389
38,610
38,832
39,053
39,276
39,498
39,721
39,945
40,168
40,393
40,617
3.45
58.812
90.996
40,842
3.85
72.112
111.57
50,078
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 60in
Palmer Bowlus Flume
3.46
59.137
91.498
41,067
3.47
59.461
92.000
41,293
3.48
59.787
92.504
41,519
3.49
60.113
93.008
41,745
3.50
60.439
93.513
41,971
*For points listed below please see footnote 1.
3.51
60.765
94.018
42,198
3.52
61.093
94.524
42,425
3.53
61.420
95.031
42,653
3.54
61.748
95.539
42,881
3.55
62.077
96.05
43,109
3.56
62.406
96.56
43,337
3.57
62.735
97.07
43,566
3.58
63.065
97.58
43,795
3.59
63.396
98.09
44,025
3.60
63.726
98.60
44,254
3.61
64.057
99.11
44,484
3.62
64.389
99.62
44,714
3.63
64.721
100.14
44,945
3.64
65.053
100.65
45,176
3.65
65.386
101.17
45,407
3.66
65.719
101.68
45,638
3.67
66.052
102.20
45,870
3.68
66.386
102.71
46,101
3.69
66.720
103.23
46,333
3.70
67.055
103.75
46,566
3.71
67.390
104.27
46,798
3.72
67.725
104.79
47,031
3.73
68.060
105.30
47,264
3.74
68.396
105.82
47,497
3.75
68.733
106.34
47,731
3.86
3.87
3.88
3.89
3.90
3.91
3.92
3.93
3.94
3.95
3.96
3.97
3.98
3.99
4.00
4.01
4.02
4.03
4.04
4.05
4.06
4.07
4.08
4.09
4.10
4.11
4.12
4.13
4.14
4.15
4.16
72.452
72.792
73.132
73.473
73.813
74.154
74.496
74.837
75.179
75.521
75.864
76.206
76.549
76.893
77.236
77.580
77.924
78.268
78.613
78.958
79.303
79.648
79.994
80.340
80.686
81.032
81.379
81.726
82.074
82.421
82.769
112.10
112.63
113.15
113.68
114.21
114.73
115.26
115.79
116.32
116.85
117.38
117.91
118.44
118.97
119.50
120.03
120.57
121.10
121.63
122.17
122.70
123.23
123.77
124.30
124.84
125.38
125.91
126.45
126.99
127.52
128.06
50,314
50,550
50,786
51,023
51,259
51,496
51,733
51,970
52,208
52,445
52,683
52,921
53,159
53,398
53,636
53,875
54,114
54,353
54,592
54,832
55,071
55,311
55,551
55,791
56,032
56,273
56,513
56,754
56,996
57,237
57,479
3.76
3.77
3.78
3.79
3.80
69.069
69.406
69.743
70.081
70.419
106.87
107.39
107.91
108.43
108.95
47,965
48,199
48,433
48,667
48,902
4.17
4.18
4.19
4.20
4.21
83.118
83.466
83.815
84.164
84.514
128.60
129.14
129.68
130.22
130.76
57,721
57,963
58,205
58,447
58,690
3.81
3.82
3.83
3.84
70.757
71.095
71.434
71.773
109.48
110.00
110.52
111.05
49,137
49,372
49,607
49,842
4.22
4.23
4.24
84.864
85.214
85.564
131.30
131.85
132.39
58,933
59,176
59,420
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
5
Flow Chart for 66in
Palmer Bowlus Flume
(feet)
0.25
0.26
0.27
0.28
0.29
0.30
0.31
0.32
0.33
0.34
0.35
0.36
0.37
0.38
0.39
0.40
0.41
0.42
0.43
0.44
0.45
0.46
0.47
0.48
0.49
0.50
0.51
0.52
0.53
0.54
0.55
0.56
0.57
0.58
0.59
0.60
0.61
0.62
0.63
0.64
MGD
0.65694
0.69570
0.73552
0.7764
0.8183
0.8613
0.9053
0.9504
0.9965
1.0436
1.0918
1.1410
1.1913
1.2426
1.2949
1.3482
1.4026
1.4579
1.5143
1.5718
1.6302
1.6897
1.7501
1.8116
1.8741
1.9376
2.0021
2.0676
2.1342
2.2017
2.2702
2.3397
2.4103
2.4818
2.5543
2.6278
2.7023
2.7778
2.8543
2.9318
CFS
1.0164
1.0764
1.1380
1.2013
1.2661
1.3326
1.4007
1.4704
1.5418
1.6147
1.6893
1.7654
1.8432
1.9225
2.0034
2.0860
2.1701
2.2558
2.3430
2.4319
2.5223
2.6143
2.7079
2.8030
2.8997
2.9979
3.0978
3.1991
3.3020
3.4065
3.5125
3.6201
3.7292
3.8399
3.9521
4.0658
4.1811
4.2979
4.4162
4.5361
GPM
456.21
483.12
510.78
539.16
568.27
598.12
628.69
659.98
692.00
724.74
758.20
792.4
827.3
862.9
899.2
936.2
974.0
1,012.5
1,051.6
1,091.5
1,132.1
1,173.4
1,215.4
1,258.1
1,301.5
1,345.6
1,390.4
1,435.9
1,482.1
1,529.0
1,576.5
1,624.8
1,673.8
1,723.5
1,773.8
1,824.9
1,876.6
1,929.0
1,982.1
2,035.9
(feet)
0.65
0.66
0.67
0.68
0.69
0.70
0.71
0.72
0.73
0.74
0.75
0.76
0.77
0.78
0.79
0.80
0.81
0.82
0.83
0.84
0.85
0.86
0.87
0.88
0.89
0.90
0.91
0.92
0.93
0.94
0.95
0.96
0.97
0.98
0.99
1.00
1.01
1.02
1.03
1.04
MGD
3.0102
3.0897
3.1701
3.2515
3.3339
3.4173
3.5017
3.5870
3.6733
3.7606
3.8489
3.9382
4.0284
4.1196
4.2118
4.3049
4.3990
4.4941
4.5901
4.6872
4.7851
4.8841
4.9840
5.0849
5.1867
5.2895
5.3933
5.4980
5.6037
5.7103
5.8179
5.9265
6.0360
6.1465
6.2579
6.3702
6.4836
6.5978
6.7131
6.8292
CFS
4.6575
4.7804
4.9049
5.0309
5.1583
5.2874
5.4179
5.5499
5.6835
5.8186
5.9551
6.0932
6.2328
6.3739
6.5166
6.6607
6.8063
6.9534
7.1020
7.2521
7.4037
7.5568
7.7114
7.8675
8.0250
8.1841
8.3446
8.5067
8.6702
8.8352
9.0017
9.1696
9.3391
9.5100
9.6824
9.8562
10.0316
10.2084
10.3866
10.5664
GPM
2,090.4
2,145.6
2,201.5
2,258.0
2,315.2
2,373.1
2,431.7
2,491.0
2,550.9
2,611.6
2,672.9
2,734.8
2,797.5
2,860.8
2,924.8
2,989.5
3,054.9
3,120.9
3,187.6
3,255.0
3,323.0
3,391.7
3,461.1
3,531.2
3,601.9
3,673.3
3,745.3
3,818.1
3,891.4
3,965.5
4,040.2
4,115.6
4,191.7
4,268.4
4,345.7
4,423.8
4,502.5
4,581.8
4,661.8
4,742.5
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 66in
Palmer Bowlus Flume
1.05
1.06
1.07
1.08
1.09
1.10
1.11
1.12
1.13
1.14
1.15
1.16
1.17
1.18
1.19
1.20
1.21
1.22
1.23
1.24
1.25
1.26
1.27
1.28
1.29
1.30
1.31
1.32
1.33
1.34
1.35
1.36
1.37
1.38
1.39
1.40
1.41
1.42
1.43
1.44
6.9464
7.0644
7.1835
7.3034
7.4243
7.5462
7.6690
7.7928
7.9174
8.0431
8.1697
8.2972
8.4256
8.5550
8.6854
8.8167
8.9489
9.0820
9.2161
9.3511
9.4871
9.6240
9.762
9.901
10.040
10.181
10.322
10.465
10.608
10.753
10.898
11.044
11.191
11.339
11.488
11.638
11.789
11.941
12.094
12.247
10.7476
10.9303
11.1144
11.3001
11.4871
11.6757
11.8657
12.0572
12.2501
12.4445
12.6403
12.8376
13.0364
13.2366
13.4383
13.6414
13.8459
14.0520
14.2594
14.4683
14.6787
14.8905
15.1038
15.3185
15.5346
15.7522
15.9712
16.1917
16.4136
16.6369
16.8617
17.0879
17.3156
17.5447
17.7752
18.0071
18.2405
18.4754
18.7116
18.9493
4,823.9
4,905.9
4,988.5
5,071.8
5,155.8
5,240.4
5,325.7
5,411.6
5,498.2
5,585.5
5,673.4
5,761.9
5,851.1
5,941.0
6,031.5
6,122.7
6,214.5
6,307.0
6,400.1
6,493.8
6,588.3
6,683.3
6,779.0
6,875.4
6,972.4
7,070.1
7,168.4
7,267.3
7,366.9
7,467.2
7,568.1
7,669.6
7,771.8
7,874.6
7,978.1
8,082.2
8,186.9
8,292.3
8,398.3
8,505.0
1.45
1.46
1.47
1.48
1.49
1.50
1.51
1.52
1.53
1.54
1.55
1.56
1.57
1.58
1.59
1.60
1.61
1.62
1.63
1.64
1.65
1.66
1.67
1.68
1.69
1.70
1.71
1.72
1.73
1.74
1.75
1.76
1.77
1.78
1.79
1.80
1.81
1.82
1.83
1.84
12.402
12.557
12.714
12.871
13.029
13.188
13.348
13.509
13.671
13.834
13.998
14.163
14.328
14.495
14.662
14.830
15.000
15.170
15.341
15.513
15.686
15.860
16.034
16.210
16.386
16.564
16.742
16.922
17.102
17.283
17.465
17.6478
17.8316
18.0163
18.2020
18.3885
18.5760
18.7643
18.9536
19.1438
19.1884
19.4289
19.6709
19.9143
20.1591
20.4053
20.6530
20.9021
21.1526
21.4045
21.6579
21.9127
22.1689
22.4265
22.6855
22.9459
23.2078
23.4711
23.7358
24.0019
24.2694
24.5383
24.8087
25.0804
25.3536
25.6282
25.9041
26.1815
26.4603
26.7405
27.0221
27.3052
27.5896
27.8754
28.1626
28.4512
28.7413
29.0327
29.3255
29.6198
8,612.3
8,720.3
8,828.9
8,938.1
9,048.0
9,158.6
9,269.7
9,381.5
9,493.9
9,607.0
9,720.7
9,835.1
9,950.1
10,065.7
10,182.0
10,298.9
10,416.4
10,534.5
10,653.4
10,772.8
10,892.9
11,013.6
11,134.9
11,256.9
11,379.5
11,502.7
11,626.6
11,751.1
11,876.2
12,002.0
12,128.4
12,255.4
12,383.1
12,511.3
12,640.3
12,769.8
12,900.0
13,030.8
13,162.2
13,294.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 66in
Palmer Bowlus Flume
1.85
1.86
1.87
1.88
1.89
1.90
1.91
1.92
1.93
1.94
1.95
1.96
1.97
1.98
1.99
2.00
2.01
2.02
2.03
2.04
2.05
2.06
2.07
2.08
2.09
2.10
2.11
2.12
2.13
2.14
2.15
2.16
2.17
2.18
2.19
2.20
2.21
2.22
2.23
2.24
19.3348
19.5268
19.7197
19.9135
20.1082
20.3037
20.5002
20.6976
20.8959
21.0951
21.2952
21.4962
21.6981
21.9009
22.1046
22.3091
22.5146
22.7210
22.9283
23.1365
23.3455
23.5555
23.7664
23.9781
24.1908
24.4043
24.6188
24.8341
25.0503
25.2674
25.4855
25.7044
25.9242
26.1449
26.3664
26.5889
26.8123
27.0365
27.2617
27.4877
29.9154
30.2124
30.5109
30.8107
31.1119
31.4145
31.7185
32.0239
32.3307
32.6389
32.9485
33.2595
33.5719
33.8856
34.2008
34.5173
34.8353
35.1546
35.4753
35.7974
36.1209
36.4457
36.7720
37.0996
37.4286
37.7591
38.0908
38.4240
38.7586
39.0945
39.4318
39.7705
40.1106
40.4521
40.7949
41.1391
41.4847
41.8317
42.1800
42.5297
13,427.0
13,560.3
13,694.2
13,828.8
13,964.0
14,099.8
14,236.3
14,373.3
14,511.0
14,649.4
14,788.3
14,927.9
15,068.1
15,208.9
15,350.4
15,492.4
15,635.1
15,778.5
15,922.4
16,067.0
16,212.2
16,358.0
16,504.4
16,651.5
16,799.1
16,947.4
17,096.4
17,245.9
17,396.0
17,546.8
17,698.2
17,850.2
18,002.9
18,156.1
18,310.0
18,464.5
18,619.6
18,775.3
18,931.7
19,088.7
2.25
2.26
2.27
2.28
2.29
2.30
2.31
2.32
2.33
2.34
2.35
2.36
2.37
2.38
2.39
2.40
2.41
2.42
2.43
2.44
2.45
2.46
2.47
2.48
2.49
2.50
2.51
2.52
2.53
2.54
2.55
2.56
2.57
2.58
2.59
2.60
2.61
2.62
2.63
2.64
27.7146
27.9424
28.1711
28.4007
28.6312
28.863
29.095
29.328
29.562
29.797
30.033
30.269
30.507
30.745
30.985
31.225
31.466
31.708
31.951
32.195
32.439
32.685
32.931
33.178
33.427
33.676
33.925
34.176
34.428
34.681
34.934
35.188
35.443
35.700
35.956
36.214
36.473
36.733
36.993
37.254
42.8808
43.2333
43.5871
43.9424
44.2990
44.6569
45.0163
45.3770
45.7391
46.1025
46.4673
46.8335
47.2011
47.5700
47.9403
48.3120
48.6850
49.0594
49.4352
49.8123
50.1908
50.5707
50.9519
51.3345
51.7184
52.1038
52.4904
52.8785
53.2679
53.6587
54.0508
54.4443
54.8391
55.2353
55.6329
56.0318
56.4321
56.8337
57.2367
57.6411
19,246.2
19,404.4
19,563.3
19,722.7
19,882.7
20,043.4
20,204.7
20,366.6
20,529.1
20,692.2
20,856.0
21,020.3
21,185.3
21,350.9
21,517.1
21,683.9
21,851.3
22,019.4
22,188.0
22,357.3
22,527.2
22,697.7
22,868.8
23,040.5
23,212.8
23,385.8
23,559.3
23,733.5
23,908.3
24,083.7
24,259.7
24,436.3
24,613.5
24,791.3
24,969.8
25,148.8
25,328.5
25,508.7
25,689.6
25,871.1
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 66in
Palmer Bowlus Flume
2.65
2.66
2.67
2.68
2.69
2.70
2.71
2.72
2.73
2.74
2.75
2.76
2.77
2.78
2.79
2.80
2.81
2.82
2.83
2.84
2.85
2.86
2.87
2.88
2.89
2.90
2.91
2.92
2.93
2.94
2.95
2.96
2.97
2.98
2.99
3.00
3.01
3.02
3.03
3.04
37.517
37.780
38.044
38.309
38.574
38.841
39.108
39.377
39.646
39.916
40.187
40.459
40.731
41.005
41.2795
41.5548
41.8310
42.1081
42.3860
42.6648
42.9445
43.2250
43.5065
43.7888
44.0719
44.3559
44.6408
44.9266
45.2133
45.5008
45.7891
46.0784
46.3685
46.6595
46.9513
47.2440
47.5376
47.8321
48.1274
48.4235
58.0468
58.4538
58.8622
59.2720
59.6831
60.0956
60.5094
60.9246
61.3412
61.7590
62.1783
62.5989
63.0208
63.4441
63.8688
64.2947
64.7221
65.1508
65.5808
66.0122
66.4449
66.8790
67.3144
67.7512
68.1893
68.6288
69.0696
69.5117
69.9552
70.4001
70.8463
71.2938
71.7426
72.1929
72.6444
73.0973
73.5515
74.0071
74.4640
74.9223
26,053.2
26,235.9
26,419.2
26,603.1
26,787.6
26,972.8
27,158.5
27,344.9
27,531.8
27,719.4
27,907.5
28,096.3
28,285.7
28,475.7
28,666.3
28,857.5
29,049.3
29,241.7
29,434.7
29,628.3
29,822.5
30,017.4
30,212.8
30,408.8
30,605.5
30,802.7
31,000.6
31,199.0
31,398.1
31,597.7
31,798.0
31,998.9
32,200.3
32,402.4
32,605.1
32,808.3
33,012.2
33,216.7
33,421.8
33,627.4
3.05
3.06
3.07
3.08
3.09
3.10
3.11
3.12
3.13
3.14
3.15
3.16
3.17
3.18
3.19
3.20
3.21
3.22
3.23
3.24
3.25
3.26
3.27
3.28
3.29
3.30
3.31
3.32
3.33
3.34
3.35
3.36
3.37
3.38
3.39
3.40
3.41
3.42
3.43
3.44
48.7206
49.0185
49.3173
49.6169
49.9174
50.2188
50.5210
50.8241
51.1281
51.4329
51.7386
52.0451
52.3525
52.6608
52.9699
53.2799
53.5908
53.9025
54.2151
54.5285
54.8428
55.1580
55.4740
55.7909
56.1087
56.4273
56.7467
57.0671
57.388
57.710
58.033
58.357
58.682
59.007
59.333
59.661
59.989
60.317
60.647
60.978
75.3819
75.8428
76.3051
76.7687
77.2336
77.6999
78.1675
78.6365
79.1068
79.5784
80.0514
80.5257
81.0013
81.4783
81.9566
82.4362
82.9172
83.3995
83.8831
84.3681
84.8544
85.3420
85.8310
86.3213
86.8129
87.3059
87.8002
88.2958
88.7927
89.2910
89.7906
90.2915
90.7938
91.2973
91.8022
92.3085
92.8160
93.3249
93.8351
94.3467
33,833.7
34,040.6
34,248.1
34,456.2
34,664.8
34,874.1
35,084.0
35,294.5
35,505.6
35,717.3
35,929.5
36,142.4
36,355.9
36,570.0
36,784.7
36,999.9
37,215.8
37,432.3
37,649.4
37,867.0
38,085.3
38,304.2
38,523.6
38,743.7
38,964.3
39,185.6
39,407.4
39,629.9
39,852.9
40,076.6
40,300.8
40,525.6
40,751.1
40,977.1
41,203.7
41,430.9
41,658.7
41,887.1
42,116.1
42,345.7
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 66in
Palmer Bowlus Flume
3.45
3.46
3.47
3.48
3.49
3.50
3.51
3.52
3.53
3.54
3.55
3.56
3.57
3.58
3.59
3.60
3.61
3.62
3.63
3.64
3.65
3.66
3.67
3.68
3.69
3.70
3.71
3.72
3.73
3.74
3.75
3.76
3.77
3.78
3.79
3.80
3.81
3.82
3.83
3.84
61.309
61.642
61.975
62.309
62.644
62.980
63.316
63.654
63.992
64.331
64.671
65.012
65.354
65.696
66.040
66.384
66.729
67.075
67.422
67.770
68.118
68.468
68.818
69.169
69.521
69.874
70.227
70.582
70.937
71.294
71.651
72.008
72.367
72.727
73.087
73.449
73.811
74.1738
74.5376
74.9023
94.8595
95.3737
95.8892
96.4061
96.9242
97.4437
97.9645
98.4866
99.0101
99.5349
100.0610
100.5884
101.1171
101.6472
102.1785
102.7112
103.2452
103.7806
104.3172
104.8552
105.3945
105.9351
106.4770
107.0203
107.5648
108.1107
108.6579
109.2064
109.7562
110.3074
110.8598
111.4136
111.9687
112.5251
113.0828
113.6418
114.2021
114.7638
115.3268
115.8910
42,575.9
42,806.7
43,038.1
43,270.0
43,502.6
43,735.8
43,969.5
44,203.9
44,438.8
44,674.3
44,910.5
45,147.2
45,384.5
45,622.4
45,860.9
46,100.0
46,339.7
46,579.9
46,820.8
47,062.3
47,304.3
47,547.0
47,790.2
48,034.0
48,278.4
48,523.4
48,769.0
49,015.2
49,262.0
49,509.4
49,757.3
50,005.9
50,255.0
50,504.7
50,755.1
51,006.0
51,257.5
51,509.5
51,762.2
52,015.5
3.85
75.2679
116.4566
*For points listed below, please footnote
3.86
75.6343
117.0235
3.87
76.0015
117.5917
3.88
76.3696
118.1613
3.89
76.7386
118.7321
3.90
77.1084
119.3042
3.91
77.4790
119.8777
3.92
77.8505
120.4524
3.93
78.2228
121.0285
3.94
78.5960
121.6059
3.95
78.9700
122.1846
3.96
79.3448
122.7646
3.97
79.7206
123.3459
3.98
80.0971
123.9285
3.99
80.4745
124.5125
4.00
80.8528
125.0977
4.01
81.2319
125.6842
4.02
81.6118
126.2721
4.03
81.9926
126.8612
4.04
82.3742
127.4517
4.05
82.7567
128.0435
4.06
83.1400
128.6365
4.07
83.5241
129.2309
4.08
83.9091
129.8266
4.09
84.2950
130.4236
4.10
84.6817
131.0219
4.11
85.0692
131.6215
4.12
85.4576
132.2224
4.13
85.8468
132.8246
4.14
86.2368
133.4281
4.15
86.6277
134.0329
4.16
87.0195
134.6390
4.17
87.4121
135.2464
4.18
87.8055
135.8552
4.19
88.1998
136.4652
4.20
88.5949
137.0765
4.21
88.9908
137.6891
4.22
89.3876
138.3031
4.23
89.7853
138.9183
52,269.3
52,523.8
52,778.8
53,034.4
53,290.6
53,547.4
53,804.8
54,062.8
54,321.4
54,580.5
54,840.2
55,100.6
55,361.5
55,623.0
55,885.0
56,147.7
56,411.0
56,674.8
56,939.3
57,204.3
57,469.9
57,736.1
58,002.8
58,270.2
58,538.1
58,806.7
59,075.8
59,345.5
59,615.8
59,886.7
60,158.1
60,430.2
60,702.8
60,976.0
61,249.8
61,524.2
61,799.2
62,074.7
62,350.8
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
5
Flow Chart for 66in
Palmer Bowlus Flume
4.24
4.25
4.26
4.27
4.28
4.29
4.30
4.31
4.32
4.33
4.34
4.35
4.36
4.37
4.38
4.39
4.40
4.41
4.42
4.43
4.44
4.45
4.46
4.47
4.48
4.49
4.50
4.51
4.52
4.53
4.54
4.55
4.56
4.57
4.58
4.59
4.60
90.1837
90.5831
90.9832
91.3842
91.7860
92.1887
92.5922
92.9966
93.4018
93.8078
94.2147
94.622
95.031
95.440
95.851
96.262
96.674
97.086
97.500
97.914
98.330
98.746
99.163
99.580
99.999
100.418
100.839
101.260
101.682
102.104
102.528
102.953
103.378
103.804
104.231
104.659
105.087
139.5348
140.1527
140.7718
141.3922
142.0140
142.6370
143.2613
143.8870
144.5139
145.1421
145.7716
146.4025
147.0346
147.6680
148.3027
148.9387
149.5761
150.2147
150.8546
151.4958
152.1383
152.7820
153.4271
154.0735
154.7212
155.3701
156.0204
156.6720
157.3248
157.9790
158.6344
159.2911
159.9491
160.6084
161.2691
161.9310
162.5941
62,627.6
62,904.9
63,182.8
63,461.2
63,740.3
64,019.9
64,300.1
64,580.9
64,862.3
65,144.3
65,426.8
65,710.0
65,993.7
66,278.0
66,562.9
66,848.3
67,134.4
67,421.0
67,708.2
67,996.0
68,284.4
68,573.3
68,862.8
69,153.0
69,443.7
69,734.9
70,026.8
70,319.2
70,612.3
70,905.9
71,200.0
71,494.8
71,790.1
72,086.1
72,382.6
72,679.6
72,977.3
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
6
Flow Chart for 72in
Palmer Bowlus Flume
(feet)
MGD
CFS
GPM
(feet)
MGD
CFS
GPM
3.0347
3.1177
3.2017
3.2865
3.3722
4.6953
4.8238
4.9537
5.0849
5.2176
2,107.4
2,165.1
2,223.4
2,282.3
2,341.8
0.26
0.27
0.28
0.29
0.30
0.9146
1.4151
635.15
0.61
0.62
0.63
0.64
0.65
0.31
0.32
0.33
0.34
0.35
0.9688
1.0239
1.0800
1.1371
1.1951
1.4989
1.5842
1.6710
1.7593
1.8492
672.75
711.04
750.00
789.64
829.96
0.66
0.67
0.68
0.69
0.70
3.4588
3.5463
3.6346
3.7238
3.8139
5.3515
5.4869
5.6235
5.7616
5.9010
2,401.9
2,462.7
2,524.0
2,586.0
2,648.5
0.36
0.37
0.38
0.39
0.40
1.2542
1.3142
1.3751
1.4370
1.4999
1.9405
2.0333
2.1276
2.2234
2.3207
870.95
912.6
954.9
997.9
1,041.6
0.71
0.72
0.73
0.74
0.75
3.9049
3.9967
4.0894
4.1829
4.2774
6.0417
6.1838
6.3272
6.4720
6.6180
2,711.7
2,775.5
2,839.8
2,904.8
2,970.4
0.41
0.42
0.43
0.44
0.45
1.5637
1.6285
1.6942
1.7608
1.8284
2.4194
2.5196
2.6213
2.7244
2.8289
1,085.9
1,130.9
1,176.5
1,222.8
1,269.7
0.76
0.77
0.78
0.79
0.80
4.3726
4.4688
4.5658
4.6636
4.7623
6.7655
6.9142
7.0643
7.2157
7.3684
3,036.5
3,103.3
3,170.7
3,238.6
3,307.2
0.46
0.47
0.48
0.49
0.50
1.8969
1.9664
2.0367
2.1080
2.1802
2.9350
3.0424
3.1513
3.2616
3.3733
1,317.3
1,365.5
1,414.4
1,463.9
1,514.1
0.81
0.82
0.83
0.84
0.85
4.8619
4.9623
5.0636
5.1657
5.2687
7.5225
7.6778
7.8345
7.9925
8.1518
3,376.3
3,446.0
3,516.4
3,587.3
3,658.8
0.51
0.52
0.53
0.54
0.55
2.2534
2.3274
2.4024
2.4783
2.5551
3.4865
3.6011
3.7171
3.8345
3.9533
1,564.9
1,616.3
1,668.3
1,721.0
1,774.3
0.86
0.87
0.88
0.89
0.90
5.3725
5.4771
5.5826
5.6890
5.7962
8.3125
8.4744
8.6376
8.8022
8.9680
3,730.9
3,803.6
3,876.8
3,950.7
4,025.1
0.56
0.57
0.58
0.59
0.60
2.6328
2.7113
2.7908
2.8712
2.9525
4.0735
4.1951
4.3180
4.4424
4.5682
1,828.3
1,882.9
1,938.1
1,993.9
2,050.3
0.91
0.92
0.93
0.94
0.95
5.9042
6.0131
6.1229
6.2334
6.3448
9.1352
9.304
9.473
9.645
9.817
4,100.2
4,175.8
4,252.0
4,328.8
4,406.1
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
1
Flow Chart for 72in
Palmer Bowlus Flume
0.96
0.97
0.98
0.99
1.00
6.4571
6.5702
6.6841
6.7989
6.9145
9.991
10.166
10.342
10.519
10.698
4,484.1
4,562.6
4,641.7
4,721.4
4,801.7
1.31
1.32
1.33
1.34
1.35
10.917
11.059
11.203
11.347
11.493
16.890
17.111
17.333
17.557
17.782
7,580.9
7,680.0
7,779.7
7,880.1
7,981.0
1.01
1.02
1.03
1.04
1.05
7.0310
7.1482
7.2664
7.3854
7.5052
10.878
11.060
11.243
11.427
11.612
4,882.6
4,964.1
5,046.1
5,128.7
5,211.9
1.36
1.37
1.38
1.39
1.40
11.639
11.786
11.934
12.083
12.232
18.008
18.235
18.464
18.694
18.926
8,082.5
8,184.6
8,287.3
8,390.7
8,494.6
1.06
1.07
1.08
1.09
1.10
7.6258
7.7473
7.8696
7.9928
8.1168
11.799
11.987
12.176
12.367
12.559
5,295.7
5,380.1
5,465.0
5,550.6
5,636.7
1.41
1.42
1.43
1.44
1.45
12.383
12.534
12.687
12.840
12.994
19.159
19.393
19.629
19.866
20.104
8,599.1
8,704.3
8,810.1
8,916.5
9,023.5
1.11
1.12
1.13
1.14
1.15
8.2417
8.3674
8.4939
8.6213
8.7495
12.752
12.946
13.142
13.339
13.537
5,723.4
5,810.7
5,898.5
5,987.0
6,076.0
1.46
1.47
1.48
1.49
1.50
13.149
13.305
13.461
13.619
13.778
20.344
20.585
20.828
21.072
21.317
9,131.1
9,239.3
9,348.2
9,458
9,568
1.16
1.17
1.18
1.19
1.20
8.8786
9.0085
9.1393
9.2709
9.403
13.737
13.938
14.141
14.344
14.549
6,165.7
6,255.9
6,346.7
6,438.1
6,530.1
1.51
1.52
1.53
1.54
1.55
13.937
14.097
14.259
14.421
14.584
21.564
21.812
22.061
22.312
22.565
9,679
9,790
9,902
10,014
10,128
1.21
1.22
1.23
1.24
1.25
9.537
9.671
9.806
9.942
10.078
14.755
14.963
15.172
15.382
15.593
6,622.6
6,715.8
6,809.6
6,903.9
6,998.8
1.56
1.57
1.58
1.59
1.60
14.748
14.913
15.079
15.245
15.413
22.818
23.074
23.330
23.588
23.848
10,242
10,356
10,471
10,587
10,704
1.26
1.27
1.28
1.29
1.30
10.216
10.354
10.494
10.634
10.775
15.806
16.020
16.236
16.453
16.671
7,094.4
7,190.5
7,287.2
7,384.5
7,482.4
1.61
1.62
1.63
1.64
1.65
15.582
15.751
15.922
16.093
16.265
24.108
24.371
24.634
24.900
25.166
10,821
10,938
11,057
11,176
11,295
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
2
Flow Chart for 72in
Palmer Bowlus Flume
1.66
1.67
1.68
1.69
1.70
16.439
16.613
16.788
16.964
17.141
25.434
25.704
25.975
26.247
26.521
11,416
11,537
11,658
11,781
11,904
2.01
2.02
2.03
2.04
2.05
23.118
23.327
23.538
23.749
23.961
35.769
36.093
36.418
36.745
37.074
16,054
16,200
16,346
16,492
16,640
1.71
1.72
1.73
1.74
1.75
17.319
17.498
17.678
17.859
18.041
26.797
27.074
27.352
27.632
27.913
12,027
12,151
12,276
12,402
12,528
2.06
2.07
2.08
2.09
2.10
24.175
24.389
24.605
24.821
25.039
37.404
37.736
38.069
38.404
38.741
16,788
16,937
17,087
17,237
17,388
1.76
1.77
1.78
1.79
1.80
18.224
18.407
18.592
18.778
18.965
28.196
28.480
28.766
29.054
29.343
12,655
12,783
12,911
13,040
13,170
2.11
2.12
2.13
2.14
2.15
25.258
25.478
25.698
25.920
26.144
39.079
39.420
39.761
40.105
40.450
17,540
17,693
17,846
18,000
18,155
1.81
1.82
1.83
1.84
1.85
19.152
19.341
19.531
19.721
19.913
29.633
29.925
30.218
30.513
30.810
13,300
13,431
13,563
13,695
13,829
2.16
2.17
2.18
2.19
2.20
26.368
26.593
26.820
27.047
27.276
40.797
41.146
41.496
41.848
42.202
18,311
18,467
18,625
18,783
18,941
1.86
1.87
1.88
1.89
1.90
20.106
20.299
20.494
20.690
20.887
31.108
31.408
31.709
32.012
32.316
13,962
14,097
14,232
14,368
14,505
2.21
2.22
2.23
2.24
2.25
27.506
27.736
27.968
28.201
28.436
42.557
42.915
43.273
43.634
43.997
19,101
19,261
19,422
19,584
19,747
1.91
1.92
1.93
1.94
1.95
21.084
21.283
21.483
21.684
21.885
32.622
32.930
33.239
33.550
33.862
14,642
14,780
14,919
15,058
15,198
2.26
2.27
2.28
2.29
2.30
28.671
28.908
29.145
29.384
29.624
44.361
44.727
45.094
45.464
45.835
19,910
20,075
20,240
20,405
20,572
1.96
1.97
1.98
1.99
2.00
22.088
22.292
22.497
22.703
22.910
34.176
34.491
34.808
35.127
35.447
15,339
15,481
15,623
15,766
15,910
2.31
2.32
2.33
2.34
2.35
29.865
30.107
30.350
30.595
30.840
46.208
46.582
46.959
47.337
47.717
20,739
20,908
21,077
21,246
21,417
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
3
Flow Chart for 72in
Palmer Bowlus Flume
2.36
2.37
2.38
2.39
2.40
31.087
31.335
31.584
31.834
32.086
48.099
48.483
48.868
49.255
49.644
21,588
21,760
21,933
22,107
22,282
2.71
2.72
2.73
2.74
2.75
40.466
40.756
41.047
41.338
41.632
62.611
63.059
63.508
63.960
64.414
28,102
28,303
28,505
28,707
28,911
2.41
2.42
2.43
2.44
2.45
32.338
32.592
32.847
33.103
33.360
50.035
50.428
50.822
51.218
51.616
22,457
22,633
22,810
22,988
23,167
2.76
2.77
2.78
2.79
2.80
41.926
42.221
42.518
42.816
43.115
64.869
65.326
65.785
66.246
66.709
29,115
29,320
29,527
29,733
29,941
2.46
2.47
2.48
2.49
2.50
33.619
33.878
34.139
34.401
34.664
52.016
52.418
52.821
53.227
53.634
23,346
23,527
23,708
23,890
24,072
2.81
2.82
2.83
2.84
2.85
43.416
43.717
44.020
44.324
44.629
67.174
67.641
68.109
68.579
69.052
30,150
30,359
30,569
30,781
30,993
2.51
2.52
2.53
2.54
2.55
34.929
35.194
35.461
35.729
35.998
54.043
54.453
54.866
55.281
55.697
24,256
24,440
24,626
24,812
24,999
2.86
2.87
2.88
2.89
2.90
44.936
45.243
45.552
45.862
46.173
69.526
70.002
70.479
70.959
71.441
31,205
31,419
31,633
31,849
32,065
2.56
2.57
2.58
2.59
2.60
36.268
36.540
36.812
37.086
37.361
56.115
56.535
56.957
57.381
57.806
25,186
25,375
25,564
25,754
25,945
2.91
2.92
2.93
2.94
2.95
46.486
46.799
47.114
47.430
47.747
71.924
72.409
72.896
73.385
73.876
32,282
32,499
32,718
32,938
33,158
2.61
2.62
2.63
2.64
2.65
37.638
37.915
38.194
38.474
38.755
58.234
58.663
59.094
59.527
59.962
26,137
26,330
26,523
26,718
26,913
2.96
2.97
2.98
2.99
3.00
48.066
48.385
48.706
49.028
49.351
74.369
74.863
75.359
75.857
76.357
33,379
33,601
33,824
34,047
34,272
2.66
2.67
2.68
2.69
2.70
39.037
39.320
39.605
39.891
40.178
60.399
60.838
61.278
61.720
62.165
27,109
27,306
27,503
27,702
27,901
3.01
3.02
3.03
3.04
3.05
49.675
50.001
50.328
50.655
50.984
76.859
77.363
77.868
78.376
78.885
34,497
34,723
34,950
35,177
35,406
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
4
Flow Chart for 72in
Palmer Bowlus Flume
3.06
3.07
3.08
3.09
3.10
51.315
51.646
51.979
52.312
52.647
79.396
79.908
80.423
80.939
81.457
35,635
35,865
36,096
36,328
36,560
3.41
3.42
3.43
3.44
3.45
63.584
63.954
64.325
64.697
65.070
98.38
98.95
99.53
100.10
100.68
44,156
44,413
44,670
44,928
45,188
3.11
3.12
3.13
3.14
3.15
52.983
53.320
53.659
53.998
54.339
81.977
82.499
83.022
83.547
84.074
36,794
37,028
37,263
37,499
37,735
3.46
3.47
3.48
3.49
3.50
65.444
65.819
66.195
66.572
66.950
101.26
101.84
102.42
103.00
103.59
45,447
45,708
45,969
46,231
46,493
3.16
3.17
3.18
3.19
3.20
54.681
55.023
55.367
55.713
56.059
84.603
85.134
85.666
86.200
86.736
37,973
38,211
38,450
38,689
38,930
3.51
3.52
3.53
3.54
3.55
67.329
67.709
68.090
68.471
68.854
104.17
104.76
105.35
105.94
106.53
46,756
47,020
47,284
47,550
47,815
3.21
3.22
3.23
3.24
3.25
56.406
56.755
57.105
57.455
57.807
87.274
87.813
88.354
88.897
89.441
39,171
39,413
39,656
39,900
40,144
3.56
3.57
3.58
3.59
3.60
69.238
69.622
70.008
70.394
70.782
107.13
107.72
108.32
108.92
109.52
48,082
48,349
48,617
48,885
49,154
3.26
3.27
3.28
3.29
3.30
58.160
58.514
58.869
59.226
59.583
89.987
90.535
91.084
91.636
92.189
40,389
40,635
40,882
41,129
41,377
3.61
3.62
3.63
3.64
3.65
71.170
71.559
71.949
72.340
72.732
110.12
110.72
111.32
111.93
112.53
49,424
49,694
49,965
50,236
50,508
3.31
3.32
3.33
3.34
3.35
59.941
60.301
60.662
61.023
61.386
92.743
93.299
93.857
94.417
94.978
41,626
41,876
42,126
42,377
42,629
3.66
3.67
3.68
3.69
3.70
73.124
73.518
73.912
74.307
74.703
113.14
113.75
114.36
114.97
115.58
50,781
51,054
51,328
51,602
51,877
3.36
3.37
3.38
3.39
3.40
61.750
62.114
62.480
62.847
63.215
95.541
96.105
96.671
97.24
97.81
42,882
43,135
43,389
43,644
43,899
3.71
3.72
3.73
3.74
3.75
75.100
75.498
75.896
76.296
76.696
116.20
116.81
117.43
118.05
118.67
52,153
52,429
52,706
52,983
53,261
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
5
Flow Chart for 72in
Palmer Bowlus Flume
3.76
3.77
3.78
3.79
3.80
77.097
77.498
77.901
78.304
78.708
119.29
119.91
120.53
121.15
121.78
53,539
53,818
54,098
54,378
54,658
4.11
4.12
4.13
4.14
4.15
91.564
91.988
92.413
92.838
93.264
141.67
142.33
142.98
143.64
144.30
63,586
63,881
64,176
64,471
64,767
3.81
3.82
3.83
3.84
3.85
79.113
79.518
79.924
80.331
80.739
122.41
123.03
123.66
124.29
124.92
54,939
55,221
55,503
55,785
56,069
4.16
4.17
4.18
4.19
4.20
93.690
94.117
94.544
94.971
95.399
144.96
145.62
146.28
146.94
147.60
65,063
65,359
65,655
65,952
66,250
3.86
3.87
3.88
3.89
3.90
81.147
81.556
81.966
82.376
82.787
125.55
126.19
126.82
127.46
128.09
56,352
56,636
56,921
57,206
57,491
3.91
3.92
3.93
3.94
3.95
83.199
83.612
84.025
84.439
84.853
128.73
129.37
130.01
130.65
131.29
57,777
58,064
58,351
58,638
58,926
4.25
4.26
4.27
4.28
4.29
97.55
97.98
98.41
98.84
99.27
150.93
151.59
152.26
152.93
153.60
67,740
68,039
68,339
68,638
68,938
3.96
3.97
3.98
3.99
4.00
85.268
85.684
86.100
86.517
86.934
131.93
132.57
133.22
133.86
134.51
59,214
59,503
59,792
60,081
60,371
4.30
4.31
4.32
4.33
4.34
99.70
100.14
100.57
101.00
101.44
154.26
154.93
155.60
156.27
156.95
69,239
69,539
69,840
70,141
70,442
4.01
4.02
4.03
4.04
4.05
87.352
87.771
88.190
88.610
89.031
135.15
135.80
136.45
137.10
137.75
60,661
60,952
61,243
61,535
61,827
4.35
4.36
4.37
4.38
4.39
101.87
102.31
102.74
103.18
103.61
157.62
158.29
158.96
159.64
160.31
70,744
71,046
71,348
71,650
71,953
4.06
4.07
4.08
4.09
4.10
89.452
89.873
90.295
90.718
91.141
138.40
139.05
139.71
140.36
141.02
62,119
62,412
62,705
62,998
63,292
4.40
4.41
4.42
4.43
4.44
104.05
104.49
104.92
105.36
105.80
160.99
161.66
162.34
163.02
163.69
72,256
72,559
72,863
73,166
73,470
*For points listed below please see footnote 1.
4.21
95.828
148.27
66,547
4.22
96.257
148.93
66,845
4.23
96.686
149.60
67,143
4.24
97.116
150.26
67,442
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
6
Flow Chart for 72in
Palmer Bowlus Flume
4.45
4.46
4.47
4.48
4.49
106.24
106.67
107.11
107.55
107.99
164.37
165.05
165.73
166.41
167.09
73,774
74,079
74,384
74,689
74,994
4.81
4.82
4.83
4.84
4.85
122.26
122.72
123.17
123.62
124.08
189.17
189.87
190.57
191.28
191.98
84,904
85,219
85,535
85,850
86,167
4.50
4.51
4.52
4.53
4.54
108.43
108.87
109.31
109.75
110.19
167.77
168.45
169.13
169.81
170.50
75,299
75,605
75,911
76,217
76,524
4.86
4.87
4.88
4.89
4.90
124.54
124.99
125.45
125.91
126.37
192.69
193.39
194.10
194.81
195.52
86,483
86,801
87,118
87,436
87,755
4.55
4.56
4.57
4.58
4.59
110.64
111.08
111.52
111.96
112.41
171.18
171.86
172.55
173.23
173.92
76,830
77,137
77,445
77,752
78,060
4.91
4.92
4.93
4.94
4.95
126.83
127.29
127.75
128.21
128.67
196.23
196.94
197.65
198.37
199.08
88,074
88,393
88,713
89,034
89,355
4.60
4.61
4.62
4.63
4.64
112.85
113.29
113.74
114.18
114.63
174.60
175.29
175.98
176.67
177.36
78,368
78,676
78,985
79,293
79,603
4.96
4.97
4.98
4.99
5.00
129.13
129.60
130.06
130.53
131.00
199.80
200.52
201.24
201.96
202.68
89,677
89,999
90,322
90,646
90,970
4.65
4.66
4.67
4.68
4.69
115.07
115.52
115.97
116.41
116.86
178.04
178.73
179.43
180.12
180.81
79,912
80,222
80,532
80,842
81,152
5.01
5.02
5.03
5.04
5.05
131.46
131.93
132.40
132.87
133.35
203.41
204.13
204.86
205.59
206.32
91,295
91,620
91,947
92,274
92,601
4.70
4.71
4.72
4.73
4.74
117.31
117.76
118.20
118.65
119.10
181.50
182.19
182.89
183.58
184.28
81,463
81,774
82,086
82,398
82,710
5.06
5.07
5.08
133.82
134.29
134.77
207.05
207.78
208.52
92,930
93,259
93,589
4.75
4.76
4.77
4.78
4.79
4.80
119.55
120.00
120.45
120.90
121.36
121.81
184.97
185.67
186.37
187.07
187.77
188.47
83,022
83,335
83,648
83,962
84,275
84,590
1) Pipes/channels larger than flume may cause over discharge up to 3% (as noted in chart for upper flow ranges).
2) Flow ranges are based on meter capability, freeboard allowances and flow studies. Points beyond these may perform satisfactorily.
PHONE - 503.692.5460 | FAX - 503.210.0602 | E-MAIL - [email protected] | WEB - www.plasti-fab.com
ADDRESS - P.O. Box 100 9665 SW Tualatin-Sherwood Rd. Tualatin, Oregon 97062
7
```

### 102.87 miles - Bike MS: Ride the Riverside

Head south on MD-224 S/ Chicamuxen Rd toward Riverside Rd Turn right onto MD-224 S/ Riverside Rd Head southwest on MD-224 S/ Riverside Rd toward Ben Doane Rd Head south on MD-224 S/ Riverside Rd He...